- Circuit integrity
Circuit integrity refers to the operability of electrical circuits during a fire. It is a form of fire-resistance rating. Circuit integrity is achieved via passive fire protection means, which are subject to stringent listing and approval use and compliance.
- Cable coating is generally considered a fire retardant, which lowers the spread of flame and generation of smoke along the combustible cable jacketing. Some cable coating systems are able to achieve a measure of circuit integrity, which is demonstrated and quantified through certification listing and listing and approval use and compliance.
- An enclosure can be provided. Calcium silicate board can be used, or other methods including boards made of vermiculite, bonded and pressed with sodium silicate, flexible wraps made of ceramic fibre and rockwool, or ceramic fibre wraps treated with endothermic materials. In all cases, the installed configuration must meet the certification listing of the tested system. Alternatively, cables that achieve fire-resistance ratings on their own can be used, such as Mineral-insulated copper-clad cable, or MI cable. Mica insulated cables have also demonstrated a measure of circuit integrity for small cables.
Testing and certification
In Canada, testing is run in accordance with ULC-S101, as required by the local building code. Unfortunately, S101 is ill equipped to deal realistically with circuit integrity, particularly for enclosures. For circuit integrity cables, one simply uses a full scale wall panel test, loops the cables through the fire, energises the cables and quantifies the current carrying capacity of the cables during the fire.
There are two ways of achieving circuit integrity. One may either choose mineral insulated or otherwise fire-resistant (tested for that purpose) cables, or one may use an enclosure that was tested for that purpose. This is where "grandfathered" systems still find acceptance in certain parts in North America. A prime example of this is Canada, where the code indicates that 2" of concrete coverage over or around electrical circuits is sufficient to obtain an unquantified duration of circuit integrity. No testing documentation exists to qualify this measure, according to the Institute for Research in Construction, a part of the National Research Council of Canada. 2" of concrete, regardless of the conductor configuration, percentage fill, etc. is of course a judgment call.
Inherently fire resistive cables can be tested to UL 2196, Tests for Fire Resistive Cables, whereas enclosures for cables that are not inherently fire resistive can be tested to UL 1724 or USNRC Generic Letter 86-10, Supplement 1 in North America, or BS476 in the United Kingdom or DIN4102 in Germany.
The mechanical ducting precedent
The other grandfathered approach is drywall shaftwall systems. Drywall shaftwalls were tested as a flat wall, no corners, no turns. This approach has pretty much been negated for use around ductwork (i.e. pressurisation and grease ducting, which are required to have a fire-resistance rating) since the adoption of the more suitable ISO6944 test regime by ULC as well as Underwriters Laboratories, whereby a duct is suspended from a full scale floor slab and the enclosure is built around the duct (or an inherently fire resistant duct is similarly tested without an enclosure, since it already contains a layer of insulation), for a more realistic 3D configuration and exposure. Drywall shaftwall systems were entirely grandfathered for this application and ceased to be legally representative of due diligence the instant a properly and purposely tested system with bona fide listings became available. The same thing applies to circuit integrity enclosures.
For the mechanical ductwork, a Canadian entrepreneur got ISO6944 passed by the ULC Standards Council and then performed testing. This made all grandfathered systems legally indefencible.
This has yet to occur in Canada for circuit integrity, but it has long been standard construction work in Europe and also in the US, through work done by UL and other laboratories. Since UL is accredited by the Standards Council of Canada in Canada and its listings are considered public record up all over North America including Canada, one is ill advised to use grandfathered systems for circuit integrity anywhere.
Importantly, drywall shaftwall systems have only been qualified as straight walls in panel furnaces, not 3D enclosures with corners.
Current test methods
Germany has standardised this sort of testing via DIN4102 Part 12, dated January 1991, Fire behaviour of building materials and elements, Fire resistance of electrical cable systems, Requirements and testing. Part 12 encompasses both enclosures for cabling and bus ducts, as well as inherently fire-resistive cables, such as mineral insulated cables. Enclosures for ductwork as well as wiring are a regular part of passive fire protection there. It is also not nearly as expensive as North American qualified approaches. Typically, lightweight mineral boards are used, such as calcium silicate and sodium silicate bonded vermiculite.
The North American state of the art is UL1724 Standard for Tests of Thermal Barrier Systems for Electrical System Components as well as its cousin, UL2196 Standard for Tests of Fire Resistive Cables. UL1724 had its origin with USNRC Generic Letter 86-10 Supplement 1, issued by the Nuclear Regulatory Commission. "Supplement 1" was to address lessons learned from the widely publicised Thermo-lag 330-1 scandal, following disclosures by whistleblower Gerald W. Brown, which resulted on Congressional hearings and a large amount of remedial work.
Supplement 1 is a particularly difficult and expensive test to pass. No testing is done in anything less than a full scale fire test, running easily into 6 figure costs per burn multiplied by all the applications one desires to test. In order to pass, one must test the smallest as well as the largest application (12" and 36" cable tray, 1/2" and 6" conduit). Accordingly, the approved materials are costly, as manufacturers must get a return on the large test investment.
In concept, it is simple to devise systems that will pass the test. As far back as the 1970s, it was apparent that when one uses enough high temperature qualified insulation, such as ceramic fibre, one is assured of a rating. However, this comes at the price of significant ampacity derating. Also, the concept that more fireproofing is better, was defeated by industry tests of Thermo-lag 330-1 (which is not a fibrous insulation). No matter what was done to this material (used for fireproofing purposes over electrical circuits in full scale fire testing) by various nuclear power plant owners (USNRC licensees) who sponsored extensive testing, where more of the old Thermo-lag was applied onto the older substrate, no satisfactory results were achieved. In order for licensees to come into compliance, other methods, replacements, overlays and MI Cable were used to fix the problem. Also, since the forerunner of this testing was the USNRC, and the commercial version of it (UL1724) has undergone various revisions, the UL systems listed in the UL Building Materials directory are not necessarily qualified to the latest USNRC compliant or the latest UL version. But that does not mean that the older listings are simply discarded or that the manufacturers performed all new tests. Therefore, users must closely review the versions of the tests deemed acceptable in an end-user facility.
Ampacity derating refers to the reduction of the ability of a cable to conduct electricity. It can be tested through the use of IEEE 848 Standard Procedure for the Determination of the Ampacity Derating of Fire-Protected Cables. The more one insulates a conductor, the less current it can conduct without damage from overheating. The result of the test referenced herein is quantified in terms of percentage. If a cable is derated by 30%, it can be used to conduct only 70% as much current, thus cable of greater cross sectional area is often needed to conduct a given amount of power. The use of intumescent "windows", which shut in case of a fire, can reduce or negate the effect of ampacity derating, subject to listing and approval use and compliance.
What circuit integrity methods are used where
Ordinarily, small runs of cables are individually run with cables that are fire-resistance rated on their own. Larger bundles and trays full of wiring may be less expensive to clad or wrap on the outside. The concrete cover method is most often used in Canadian construction, as the code and common practice permit this, despite the absence of testing data that gives the required "carte blanche" for all cables and indefinite ratings.
Cladding and wrapping considerations
The added weight of the wrap systems must be included in static and seismic calculations. Fireproofing of the hanging system must also be considered. Regular maintenance must be considered, as cladding and wraps are not load-bearing and can be damaged during normal building or facility operations. Ampacity-derating may be mitigated by the use of purpose-designed intumescent or mechanically/electronically activated "windows" that permit heat venting. Like everything else in passive fire protection, all such methods are subject to stringent listing and approval use and compliance.
Circuit integrity cable considerations
Termination points and junction boxes, in other words the entire circuit, must be completely protected. Often, termination points are left out, providing a weak link. Therefore, some enclosures are needed to be used in conjunction with MI cables. One may run MI cable into a box in an electrical room. However, just because that room may be a "service room" and may be subject to compartmentalization (fire protection), this does not mean one no longer requires a rated box or wrap around the electrical outlet box or junction box where the wiring is terminated because that box may be disabled as a result of a fire within the room. The probability of electrical fires are a strong motivating factor for compartmetalisation to begin with. The cable may thus be operable but the circuit as a whole may be defeated because the junction box would not have been protected. Such omissions are not entirely uncommon in the field.
- Listing and approval use and compliance
- Fire test
- Gerald W. Brown
- Passive fire protection
- Fire protection
- Mineral-insulated copper-clad cable
- Certification listing
- DIN 4102 Fire behaviour of building materials and building components - Part 12: Circuit integrity maintenance of electric cable systems; requirements and testing
- NRC treatise on circuit integrity measures
- USNRC Generic Letter 86-10 Supplement 1 - FIRE ENDURANCE TEST ACCEPTANCE CRITERIA FOR FIRE BARRIER SYSTEMS USED TO SEPARATE REDUNDANT SAFE SHUTDOWN TRAINS WITHIN THE SAME FIRE AREA (SUPPLEMENT 1 TO GENERIC LETTER 86-10, "IMPLEMENTATION OF FIRE PROTECTION REQUIREMENTS")
- ASTM E1725 - 08 Standard Test Methods for Fire Tests of Fire-Resistive Barrier Systems for Electrical System Components
- UL1724 - FIRE TESTS FOR ELECTRICAL CIRCUIT PROTECTIVE SYSTEMS
- IEEE 848 Standard Procedure for the Determination of the Ampacity Derating of Fire-Protected Cables.
Wikimedia Foundation. 2010.
Look at other dictionaries:
Circuit extraction — The electric circuit extraction or simply circuit extraction, also netlist extraction, is the translation of an integrated circuit layout back into the electrical circuit (netlist) it is intended to represent. This extracted circuit is needed for … Wikipedia
Signal integrity — or SI is a measure of the quality of an electrical signal. In digital electronics, a stream of binary values is represented by a voltage (or current) waveform. Over short distances and at low bit rates, a simple conductor can transmit this with… … Wikipedia
Racial Integrity Act of 1924 — On March 20, 1924 the Virginia Legislature (United States) passed two closely related eugenics laws: SB 219, entitled The Racial Integrity Act [Racial Integrity Act of 1924, at Wikisource.org] and SB 281, An ACT to provide for the sexual… … Wikipedia
Integrated circuit design — Layout view of a simple CMOS Operational Amplifier ( inputs are to the left and the compensation capacitor is to the right ). The metal layers are colored blue and green, the polysilicon is red and vias are crosses. Integrated circuit design, or… … Wikipedia
Electronic circuit simulation — uses mathematical models to replicate the behavior of an actual electronic device or circuit. Simulation software allows for modeling of circuit operation and is an invaluable analysis tool. Due to its highly accurate modeling capability, many… … Wikipedia
Independent circuit — In professional wrestling, the independent circuit or indy circuit refers to the many independent promotions which are much smaller than major televised promotions, particularly the current WWE and TNA promotions and WCW and ECW of the past.… … Wikipedia
Gerald W. Brown — is an American whistleblower, who concerned himself with deficiencies in passive fire protection systems in US and Canadian nuclear power plants.Thermo Lag scandalGerald W. Brown was the original whistleblower of the Thermo Lag 330 1 scandal [… … Wikipedia
Mineral-insulated copper-clad cable — MIMS redirects here. For multi isotope imaging mass spectrometry, see Isotope mass spectrometry. PVC sheathed MICC cable. Conductor cross section area is 1.5 mm²; overall diameter is 7.2 mm … Wikipedia
Passive fire protection — (PFP) is an integral component of the three components of structural fire protection and fire safety in a building. PFP attempts to contain fires or slow the spread, through use of fire resistant walls, floors, and doors (amongst other examples) … Wikipedia
работоспособность — 3.9 работоспособность: Состояние ГАП, при котором она способна выполнять заданные функции, сохраняя значения заданных параметров в пределах, установленных эксплуатационной документацией. Источник … Словарь-справочник терминов нормативно-технической документации