- Fluidized bed combustion
Fluidized bed combustion (FBC) is a combustion technology used in power plants. Fluidized beds suspend solid fuels on upward-blowing jets of air during the combustion process. The result is a turbulent mixing of gas and solids. The tumbling action, much like a bubbling fluid, provides more effective chemical reactions and heat transfer. FBC plants are more flexible than conventional plants in that they can be fired on coal and biomass, among other fuels.
FBC reduces the amount of sulfur emitted in the form of SOx emissions. Limestone is used to precipitate out sulfate during combustion, which also allows more efficient heat transfer from the boiler to the apparatus used to capture the heat energy (usually water tubes). The heated precipitate coming in direct contact with the tubes(heating by conduction) increases the efficiency. Since this allows coal plants to burn at cooler temperatures, less NOx is also emitted. However, burning at low temperatures also causes increased polycyclic aromatic hydrocarbon emissions. FBC boilers can burn fuels other than coal, and the lower temperatures of combustion (800 °C / 1500 °F ) have other added benefits as well.
There are two reasons for the rapid increase of fluidized bed combustion (FBC) in combustors. First, the liberty of choice in respect of fuels in general, not only the possibility of using fuels which are difficult to burn using other technologies, is an important advantage of fluidized bed combustion. The second reason, which has become increasingly important, is the possibility of achieving, during combustion, a low emission of nitric oxides and the possibility of removing sulfur in a simple manner by using limestone as bed material.
Fluidized-bed combustion evolved from efforts to find a combustion process able to control pollutant emissions without external emission controls (such as scrubbers-flue gas desulfurization). The technology burns fuel at temperatures of 1,400 to 1,700 °F (760-926.6 °C), well below the threshold where nitrogen oxides form (at approximately 2,500 °F / 1400 °C, the nitrogen and oxygen atoms in the combustion air combine to form nitrogen oxide pollutants); it also avoids the ash melting problems related to high combustion temperature. The mixing action of the fluidized bed brings the flue gases into contact with a sulfur-absorbing chemical, such as limestone or dolomite. More than 95% of the sulfur pollutants in coal can be captured inside the boiler by the sorbent. The reductions may be less substantial than they seem, however, as they coincide with dramatic increases in carbon (monoxide?) and polycyclic aromatic hydrocarbons emissions.
Commercial FBC units operate at competitive efficiencies, cost less than today's units, and have NO2 and SO2 emissions below levels mandated by Federal standards. Although, it has some disadvantages such as erosion on the tubes inside the boiler, uneven temperature distribution caused by clogs on the air inlet of the bed, long starting times reaching up to 48 hours in some cases.
FBC systems fit into essentially two major groups, atmospheric systems (FBC) and pressurized systems (PFBC), and two minor subgroups, bubbling (BFB) and circulating fluidized bed (CFB).
Atmospheric fluidized beds use limestone or dolomite to capture sulfur released by the combustion of coal. Jets of air suspend the mixture of sorbent and burning coal during combustion, converting the mixture into a suspension of red-hot particles that flow like a fluid. These boilers operate at atmospheric pressure.
The first-generation PFBC system also uses a sorbent and jets of air to suspend the mixture of sorbent and burning coal during combustion. However, these systems operate at elevated pressures and produce a high-pressure gas stream at temperatures that can drive a gas turbine. Steam generated from the heat in the fluidized bed is sent to a steam turbine, creating a highly efficient combined cycle system.
- A 1½ generation PFBC system increases the gas turbine firing temperature by using natural gas in addition to the vitiated air from the PFB combustor. This mixture is burned in a topping combustor to provide higher inlet temperatures for greater combined cycle efficiency. However, this uses natural gas, usually a higher priced fuel than coal.
- APFBC. In more advanced second-generation PFBC systems, a pressurized carbonizer is incorporated to process the feed coal into fuel gas and char. The PFBC burns the char to produce steam and to heat combustion air for the gas turbine. The fuel gas from the carbonizer burns in a topping combustor linked to a gas turbine, heating the gases to the combustion turbine's rated firing temperature. Heat is recovered from the gas turbine exhaust in order to produce steam, which is used to drive a conventional steam turbine, resulting in a higher overall efficiency for the combined cycle power output. These systems are also called APFBC, or advanced circulating pressurized fluidized-bed combustion combined cycle systems. An APFBC system is entirely coal-fueled.
- GFBCC. Gasification fluidized-bed combustion combined cycle systems, GFBCC, have a pressurized circulating fluidized-bed (PCFB) partial gasifier feeding fuel syngas to the gas turbine topping combustor. The gas turbine exhaust supplies combustion air for the atmospheric circulating fluidized-bed combustor that burns the char from the PCFB partial gasifier.
- CHIPPS. A CHIPPS system is similar, but uses a furnace instead of an atmospheric fluidized-bed combustor. It also has gas turbine air preheater tubes to increase gas turbine cycle efficiency. CHIPPS stands for combustion-based high performance power system.
- FutureGen zero-emissions coal-fired power plant
- JEA Northside Generating Station (Jacksonville)
- Fluidized bed
- Fluidized bed reactor
- Chemical looping combustion
- Grate firing
- Pulverised fuel firing
Wikimedia Foundation. 2010.
Look at other dictionaries:
Fluidized-bed combustion — A method of burning particulate fuel, such as coal, in which the amount of air required for combustion far exceeds that found in conventional burners. The fuel particles are continually fed into a bed of mineral ash in the proportions of 1 part … Energy terms
Fluidized bed combustion — A process for burning powdered coal that is poured in a liquid like stream with air or gases. The process reduces sulfur dioxide emissions from coal combustion. California Energy Comission. Dictionary of Energy Terms … Energy terms
Fluidized Bed Combustion — (FBC) A type of furnace or reactor in which fuel particles are combusted while suspended in a stream of hot gas … Energy terms
Fluidized bed — For other uses, see Fluidized bed (disambiguation). Oldest power station utilizing circular fluidized bed technology, in Lünen, Germany A fluidized bed is formed when a quantity of a solid particulate substance (usually present in a holding… … Wikipedia
Fluidized bed reactor — A fluidized bed reactor (FBR) is a type of reactor device that can be used to carry out a variety of multiphase chemical reactions. In this type of reactor, a fluid (gas or liquid) is passed through a granular solid material (usually a catalyst… … Wikipedia
Fluidized bed (disambiguation) — Articles on Fluidized bed include:* Fluidized bed * Fluidized bed combustion * Fluidized bed dryer * Fluidized bed reactor * Coffee roasting using a fluidized bed … Wikipedia
fluidized bed — noun a) An industrial in which a quantity of a solid particulate substance is caused to float in a stream of a fluid (usually air or other gas) in order to create conditions in which many chemical, combustion and drying reactions take place… … Wiktionary
Combustión en lecho fluido — La combustión en lecho fluido (Fluidized bed combustion,FBC en inglés) es una tecnología de combustión usada en centrales eléctricas. Esta tecnología permite una mayor flexibilidad en el uso de combustible: carbón, biomasa,basura etc, además de… … Wikipedia Español
Chemical looping combustion — (CLC) typically employs a dual fluidized bed system (circulating fluidized bed process) where a metal oxide is employed as a bed material providing the oxygen for combustion in the fuel reactor. The reduced metal is then transferred to the second … Wikipedia
Westinghouse Combustion Turbine Systems Division — Part of the Westinghouse Power Generation group, the Combustion Turbine Systems Division (CTSD) was originally located, along with the Steam Turbine Systems Division (STSD), in a major industrial facility in Tinicum Township (Delaware County,… … Wikipedia