- Damper (architecture)
A damper is a valve or plate that stops or regulates the flow of air inside a duct,
chimney, VAV box, air handler, or other air handling equipment. A damper may be used to cut off central air conditioning(heating or cooling) to an unused room, or to regulate it for room-by-room temperatureand climate control. Its operation can be manual or automatic. Manual dampers are turned by a handle on the outside of a duct. Automatic dampers are used to regulate airflow constantly and are operated by electric or pneumatic motors, in turn controlled by a thermostator building automationsystem.
In a chimney
flue, a damper closes off the flue to keep the weather(and birds and other animals) out and warm or cool air in. This is usually done in the summer, but also sometimes in the winter between uses. In some cases, the damper may also be partly closed to help control the rate of combustion. The damper may be accessible only by reaching up into the fireplaceby hand or with a woodpoker, or sometimes by a lever or knob that sticks down or out. On a woodburning stoveor similar device, it is usually a handle on the ventduct as in an air conditioning system. Forgetting to open a damper before beginning a firecan cause serious smokedamage to the interior of a home, if not a house fire.
Automated zone dampers
A zone damper (also known as a Volume Control Damper or VCD) is a specific type of damper used to control the flow of air in an
HVACheating or cooling system. In order to improve efficiency and occupant comfort, HVAC systems are commonly divided up into multiple zones. For example, in a house, the main floor may be served by one heating zone while the upstairs bedrooms are served by another. In this way, the heat can be directed principally to the main floor during the day and principally to the bedrooms at night, allowing the unoccupied areas to cool down.
Zone dampers as used in home HVAC systems are usually electrically powered. In large commercial installations,
vacuumor compressed airmay be used instead. In either case, the motor is usually connected to the damper via a mechanical coupling.
For electrical zone dampers, there are two principal designs.
In one design, the motor is often a small
shaded-pole synchronous motorcombined with a rotary switch that can disconnect the motor at either of the two stopping points ("damper open" or "damper closed"). In this way, applying power to the "open damper" terminal causes the motor to run until the damper is open while applying power at the "close damper" terminal causes the motor to run until the damper is closed. The motor is commonly powered from the same 24 voltac power source that is used for the rest of the control system. This allows the zone dampers to be directly controlled by low-voltage thermostats and wired with low-voltage wiring. Because simultaneous closure of all dampers might harm the furnace or air handler, this style of damper is often designed to only obstruct a portion of the air duct, for example, 75%.
Another style of electrically powered damper uses a spring-return mechanism and a shaded-pole synchronous motor. In this case, the damper is normally opened by the force of the spring but can be closed by the force of the motor. Removal of electrical power re-opens the damper. This style of damper is advantageous because it is "fail safe"; if the control to the damper fails, the damper opens and allows air to flow. However, in most applications "fail safe" indicates the damper will close upon loss of power thus preventing the spread of smoke and fire to other areas. These dampers also may allow adjustment of the "closed" position so that they only obstruct, for example, 75% of the air flow when closed.
For vacuum- or pneumatically-operated zone dampers, the thermostat usually switches the pressure or vacuum on or off, causing a spring-loaded rubber diaphragm to move and actuate the damper. As with the second style of electrical zone dampers, these dampers automatically return to the default position without the application of any power, and the default position is usually "open", allowing air to flow. Like the second style of electrical zone damper, these dampers may allow adjustment of the "closed" position.
Highly sophisticated systems may use some form of
building automationsuch as BACnetor LonWorksto control the zone dampers. The dampers may also support positions other than fully open or fully closed and are usually capable of reporting their current position and, often, the temperature and volume of the air flowing past the smart damper.
Regardless of the style of damper employed, the systems are often designed so that when no thermostat is calling for air, all dampers in the system are opened. This allows air to continue to flow while the heat exchanger in a furnace cools down after a heating period completes.
Comparison to multiple furnaces/air handlers
Multiple zones can be implemented using either multiple, individually-controlled furnaces/air handlers or a single furnace/air handler and multiple zone dampers. Each approach has advantages and disadvantages.
Multiple furnaces/air handlers
* Simple mechanical and control design ("SPST thermostats")
* Redundancy: If one zone furnace fails, the others can remain working
* Cost. Furnaces cost much more than zone dampers
* Power consumption. Operating furnaces draw power whereas a zone damper only draws power while in motion from one state to the other (or, in some cases, a very small amount of power while holding closed).
* Power consumption.
* Zone dampers are not 100% reliable. The motor-to-open/motor-to-closed style of electrically operated zone dampers aren't "fail safe" (that is, they do not fail to the open condition). However, zone dampers that are of the "Normally Open" type are fail-safe, in that they will fail to the open condition.
* No inherent redundancy for the furnace. A system with zone dampers is dependent upon a single furnace. If it fails, the system becomes completely inoperable.
* The system can be harder to design, requiring both "SPDT" thermostats (or
relays) and the ability of the system to withstand the fault condition whereby all zone dampers are closed simultaneously.
Fire dampers are fitted where ductwork passes through fire compartment walls / fire curtains as part of a fire control strategy. In normal circumstances, these dampers are held open by means of fusible links. When subjected to heat, these links fracture and allow the damper to close under the influence of the integral closing spring. The links are attached to the damper such that the dampers can be released manually for testing purposes. The damper is provided with an access door in the adjacent ductwork for the purpose of inspection and resetting in the event of closure.
Variable air volume(VAV)
* [http://dampersandexpansionjoints.com/damper-expansion-joint-faq.html Flextor Dampers FAQ]
Wikimedia Foundation. 2010.
Look at other dictionaries:
Architecture of New York City — The Empire State Building (foreground) and Chrysler Building are some of the finest examples of Art Deco architecture A building form closely associated with New York City is the skyscraper, which has controversially shifted many commercial and… … Wikipedia
Tuned mass damper — La boule d amortissement du gratte ciel Taipei 101 pèse 660 tonnes. Un Tuned mass damper est un dispositif installé sur des structures du génie civil (ponts, viaducs, antennes...) permettant la réduction des oscillations provoquées par le vent… … Wikipédia en Français
Comcast Center (Philadelphia) — Comcast Center Former names One Pennsylvania Plaza General information Type Commercial offices … Wikipedia
John Hancock Tower — Infobox Skyscraper building name= Hancock Place location= 200 Clarendon Street, Boston, Massachusetts, United States roof= 790 ft (240.7 m) height stories= 60 construction period= 1968 1976 use= Office architect= I.M. Pei Partners developer=… … Wikipedia
Russia — /rush euh/, n. 1. Also called Russian Empire. Russian, Rossiya. a former empire in E Europe and N and W Asia: overthrown by the Russian Revolution 1917. Cap.: St. Petersburg (1703 1917). 2. See Union of Soviet Socialist Republics. 3. See Russian… … Universalium
Business and Industry Review — ▪ 1999 Introduction Overview Annual Average Rates of Growth of Manufacturing Output, 1980 97, Table Pattern of Output, 1994 97, Table Index Numbers of Production, Employment, and Productivity in Manufacturing Industries, Table (For Annual… … Universalium
Gottfried Silbermann — (January 14, 1683 August 4, 1753) was an influential German constructor of keyboard instruments. He built harpsichords, clavichords, organs, and pianos; his modern reputation rests mainly on the latter two.LifeVery little is known about… … Wikipedia
Duplicating machines — were the predecessors of modern document reproduction technology. They have now been replaced by digital duplicators, scanners, laser printers and photocopiers, but for many years they were the primary means of reproducing documents for limited… … Wikipedia
Construction Parasismique — Taipei 101, équipé accordé par tuned mass damper, est le deuxième plus grand gratte ciel du monde après Burj dubai La Construction parasismique est l étude du comportement des bâtiments et structures sujets à un chargement dynamique du type… … Wikipédia en Français
Construction antiséismique — Construction parasismique Taipei 101, équipé accordé par tuned mass damper, est le deuxième plus grand gratte ciel du monde après Burj dubai La Construction parasismique est l étude du comportement des bâtiments et structures sujets à un… … Wikipédia en Français