- Actual cubic foot per minute
The cubic foot per minute (CFM) or actual cubic foot per minute (ACFM) is a unit of volumetric capacity commonly used by manufacturers of
blowers and compressors. Since the volumetric capacity refers to the volume of airor other gas at the inlet to the unit, it is also often referred to as Inlet CFM (ICFM). All three terms (CFM, ACFM or ICFM) are used interchangeably to mean basically the same thing.
Standard Cubic Feet per Minute (SCFM) is a volumetric flow-rate corrected to a set of "standardized" conditions of pressure, temperature, and sometimes relative humidity. The standard conditions are often defined as some pressure (e.g., 14.7 psia), some temperature (e.g., 68°F) and some relative humidity (e.g., 36% or 0 %) depending on the "standard" used. (See
Standard conditions for temperature and pressure).
Actual Cubic Feet per Minute (ACFM) is the volume of gas flowing anywhere in a system independent of its density. If the system were moving air at exactly the "standard" condition, then ACFM would equal SCFM. Unfortunately, this usually is not the case as the most important change between these two definitions is the pressure. To move air a positive pressure or a vacuum must be created. When positive pressure is applied to a standard cubic foot of air or other gas, it gets smaller. When a vacuum is applied to a standard cubic foot of air or gas , it expands. The volume of air or gas after it is pressurized or rarefied is referred to as its "actual" volume.
The term CFM has no single definition that applies to all instances. In the most basic sense, CFM means cubic feet per minute, but since air is a compressible gas, this term can be ambiguous. For instance, a centrifugal fan is a constant CFM device or a constant volume device, meaning that, at a constant fan speed, a centrifugal fan will pump a constant volume of air rather than a constant mass. This means that the air velocity in a system is fixed even though mass flow rate through the fan is not.
Centrifugal Fan Ratings
Ratings found in centrifugal-fan performance tables and curves are based on standard air (SCFM). Fan manufacturers define standard air as clean, dry air with a density of 0.075 pounds mass per cubic foot, with the barometric pressure at sea level of 29.92 inches of mercury and a temperature of 70°F. Selecting a centrifugal fan to operate at conditions other than standard air requires adjustment to both static pressure and brake horsepower. The volume of air will not be affected in a given system because a fan will move the same amount of air regardless of the air density. If a centrifugal fan is to operate at a non-standard density, then corrections must be made to static pressure and brake horsepower. At higher than standard elevation (sea level) and higher than standard temperature (70°F), air density is lower than standard density (0.075 pounds per cubic foot). Centrifugal fans that are specified for continuous operation at higher temperatures need to be selected taking into account air density corrections. Again, a centrifugal fan is a constant volume device that will move the same amount of air at two different temperatures.
If, for example, a centrifugal fan moves 1,000 CFM at 70ºF it will also move 1,000 CFM at 200ºF. The air volume delivered by the centrifugal fan is not affected by density. However, since the 200°F air weighs much less than the 70ºF air, the centrifugal fan will create less static pressure and will require less brake horsepower. Selecting a centrifugal fan to operate at conditions other than standard air requires adjustment to both static pressure and brake horsepower. When a centrifugal fan is specified for a given CFM and static pressure at conditions other than standard, an air density correction factor must be applied to select the proper size fan to meet the new condition. Since 200°F air weighs only 80% of 70°F air, the centrifugal fan will create less pressure. To get the actual pressure required at 200°F, the designer would have to multiply the pressure at standard conditions by an air density correction factor of 1.25 (i.e., 1.0 / 0.80) to get the system to operate correctly. To get the actual horsepower at 200°F, the designer would have to divide the brake horsepower at standard conditions by the air density correction factor.
Air Movement and Control Association (AMCA)
The centrifugal fan performance tables provide the fan RPM and brake horsepower requirements for the given CFM and static pressure at standard air density (0.075 pounds per cubic foot). When the centrifugal fan performance is not at standard conditions, the performance must be converted to standard conditions before entering the performance tables. Centrifugal fans rated by the Air Movement and Control Association (AMCA) are tested in laboratories with test setups that simulate installations that are typical for that type of fan. Usually they are tested and rated as one of four standard installation types as designated in AMCA Standard 210.
AMCA Standard 210 defines uniform methods for conducting laboratory tests on housed fans to determine airflow rate, pressure, power and efficiency, at a given speed of rotation. The purpose of AMCA Standard 210 is to define exact procedures and conditions of fan testing so that ratings provided by various manufacturers are on the same basis and may be compared. For this reason, fans must be rated in SCFM.
* [http://www.gerardgarcia.com/ACFM-versus-SCFM.html ACFM versus SCFM for ASME AG-1 HEPA Filters]
* [http://www.engineeringtoolbox.com/scfm-acfm-icfm-d_1012.html SCFM versus ACFM]
* [http://www.pyebarker.com/TechTips/techtip2.htm SCFM versus ACFM]
* [http://www.sponsler.com/faqs.htm What is SCFM?]
* [http://www.fluidenergy.com/market/closer_look_air.htm SCFM, ACFM, ICFM...What Does it Mean?]
* [http://www.globaltechnologiesinc.com/engineer.php#scfm What is the difference between ACFM and SCFM?]
* [http://www.pdblowers.com/scfm_v_acfm.htm SCFM (Standard CFM) vs. ACFM (Actual CFM)]
* [http://www.pyebarker.com/TechTips/techtip2.htm SCFM vs ACFM]
* [http://www.grc.nasa.gov/WWW/K-12/airplane/fluden.html Gas Density]
* [http://www.aeromech.usyd.edu.au/aero/atmos/atmos.html Properties of Atmosphere]
* [http://www.labcair.com/reference/cfm.pdf ACFM versus SCFM versus ICFM]
* [http://www.mpair.com/library.active/nyb.engineering.letters/engltr4.pdf Temperature and Altitude Affect Fan Selection]
Standard cubic foot
Combined gas law
Wikimedia Foundation. 2010.
Look at other dictionaries:
Cubic feet per minute — (CFPM or CFM) is a non SI unit of measurement of the flow of a gas or liquid that indicates how much volume in cubic feet pass by a stationary point in one minute.Conversion factor for SI conversionsIn order to find this conversion the following… … Wikipedia
Standard cubic feet per minute — (SCFM) is the volumetric flow rate of a gas corrected to standardized conditions of temperature and pressure. It is equivalent to the molar flow rate by the ideal gas law. Conversion of SCFM to mass flow requires knowledge of the mixture averaged … Wikipedia
Standard cubic feet per minute — SCFM L acronyme SCFM est une unité de mesure de débit de gaz fréquemment utilisé dans les pays anglo saxons. SCFM signifie Standard cubic feet per minute, soit en français pied au cube par minute. Unités SI et anglo saxonnes Dans le Système… … Wikipédia en Français
SCFM — (Standard Cubic Feet per Minute) is the volumetric flow rate of a gas corrected to standardized conditions of temperature, pressure and relative humidity, thus representing a precise mass flow rate. However, great care must be taken, as the… … Wikipedia
SCFM — L acronyme SCFM est une unité de mesure de débit de gaz fréquemment utilisé dans les pays anglo saxons. SCFM signifie Standard cubic feet per minute, soit en français pied au cube par minute. Unités SI et anglo saxonnes Dans le Système… … Wikipédia en Français
Window — This article is about the part of a building. For the Microsoft operating system, see Microsoft Windows. For other uses, see Window (disambiguation) and Windows (disambiguation). Pair of windows, Old Ship Church, Hingham, Massachusetts … Wikipedia
Air flow bench — An air flow bench is a device used for testing the internal aerodynamic qualities of an engine component and is related to the more familiar wind tunnel. Used primarily for testing the intake and exhaust ports of cylinder heads of internal… … Wikipedia
river — river1 riverless, adj. riverlike, adj. /riv euhr/, n. 1. a natural stream of water of fairly large size flowing in a definite course or channel or series of diverging and converging channels. 2. a similar stream of something other than water: a… … Universalium
Wikipedia:Manual of Style/Dates and numbers — Shortcuts: WP:MOSNUM WP:DATE MOS:NUM This page is part of the Ma … Wikipedia
Wind Shear's Full Scale, Rolling Road, Automotive Wind Tunnel — Windshear Full Scale Rolling Road Wind Tunnel In January 2008 Wind Shear, a division of US machine tool builder Haas Automation, completed construction on one of the most advanced automotive wind tunnels in the world. The full scale tunnel is… … Wikipedia