- Feedwater heater
A feedwater heater is a
power plantcomponent used to pre-heat water delivered to a steamgenerating boiler. [cite book|author=British Electricity International|title=Modern Power Station Practice: incorporating modern power system practice|edition=3rd Edition (12 volume set)|publisher=Pergamon|year=1991|id=ISBN 0-08-040510-X] [cite book|author=Babcock & Wilcox Co.|title=Steam: Its Generation and Use|edition=41st edition|year=2005|id=ISBN 0-9634570-0-4] [cite book|author=Thomas C. Elliott, Kao Chen, Robert Swanekamp (coauthors)|title=Standard Handbook of Powerplant Engineering|edition=2nd edition|publisher=McGraw-Hill Professional|year=1997|id=ISBN 0-07-019435-1] Preheating the feedwater reduces the irreversibilities involved in steam generation and therefore improves the thermodynamic efficiencyof the system. [http://www.personal.utulsa.edu/~kenneth-weston/chapter2.pdf Fundamentals of Steam Power] by Kenneth Weston, University of Tulsa] This reduces plant operating costs and also helps to avoid thermal shockto the boiler metal when the feedwater is introduced back into the steam cycle.
In a steam power plant (usually modeled as a modified
Rankine cycle), feedwater heaters allow the feedwater to be brought up to the saturation temperature very gradually. This minimizes the inevitable irreversibilites associated with heat transfer to the working fluid (water). See the article on the Second Law of Thermodynamicsfor a further discussion of such irreversibilites.
Cycle discussion and explanation
It should be noted that the energy used to heat the feedwater is usually derived from steam extracted between the stages of the
steam turbine. Therefore, the steam that "would be used" to perform expansion work in the turbine (and therefore generate power) is not utilized for that purpose. The percentage of the total cycle steam mass flow used for the feedwater heater is termed the extraction fractionand must be carefully optimized for maximum power plant thermal efficiencysince increasing this fraction causes a decrease in turbine power output.
Feedwater heaters can also be "open" and "closed"
heat exchangers. An open feedwater heater is merely a direct-contact heat exchanger in which extracted steam is allowed to mix with the feedwater. This kind of heater will normally require a feed pump at both the feed inlet and outlet since the pressure in the heater is between the boiler pressure and the condenser pressure. A deaeratoris a special case of the open feedwater heater which is specifically designed to remove non-condensable gases from the feedwater.
Closed feedwater heaters are typically
shell and tube heat exchangers where the feedwater passes throughout the tubes and is heated by turbine extraction steam. These do not require separate pumps before and after the heater to boost the feedwater to the pressure of the extracted steam as with an open heater. However, the extracted steam (which is most likely almost fully condensed after heating the feedwater) must then be throttled to the condenser pressure, an isenthalpicprocess that results in some entropygain with a slight penalty on overall cycle efficiency.
Many power plants incorporate a number of feedwater heaters and may use both open and closed components.
Feedwater heaters are used in both fossil- and nuclear-fueled power plants. Smaller versions have also been installed on
steam locomotives, portable engines and stationary engines. An economiserserves a similar purpose to a feedwater heater, but is technically different. Instead of using actual cycle steam for heating, it uses the lowest-temperature flue gasfrom the furnace(and therefore does not apply to nuclear plants) to heat the water before it enters the boiler proper. This allows for the heat transfer between the furnace and the feedwater to occur across a smaller average temperature gradient (for the steam generator as a whole). System efficiency is therefore further increased when viewed with respect to actual energy content of the fuel.
Fossil fuel power plant
Thermal power plant
* [http://www.tva.gov/power/coalart.htm Power plant diagram]
* [http://www.processassociates.com/bookshelf/units/power_plant_1.htm Power Plant Reference Books]
Wikimedia Foundation. 2010.
Look at other dictionaries:
Franco-Crosti boiler — The Franco Crosti boiler is a type of boiler used for steam locomotives. It was designed in the 1930s by Attilio Franco and Dr Piero Crosti, two engineers working for the Ferrovie dello Stato (FS), the Italian state railway. Purpose The Franco… … Wikipedia
Milwaukee Road class F6 — locomotive #6409. Photo by Otto Perry at Chicago, Illinois on September 23, 1930. Power type Steam Builder Baldwin Locomotive Works Serial number … Wikipedia
PRR K5 — The Pennsylvania Railroad s class K5 was an experimental 4 6 2 Pacific type, built in 1929 to see if a larger Pacific than the standard K4s was worthwhile. Two prototypes were built, #5698 at the PRR s own Altoona Works, and #5699 by the Baldwin… … Wikipedia
Deaerator — A deaerator is a device that is widely used for the removal of oxygen and other dissolved gases from the feedwater to steam generating boilers. In particular, dissolved oxygen in boiler feedwaters will cause serious corrosion damage in steam… … Wikipedia
Economizer — Economizers, or in British English economisers, are mechanical devices intended to reduce energy consumption, or to perform another useful function like preheating a fluid. The term economizer is used for other purposes as well. Boiler,… … Wikipedia
Heating — may refer to: *HVAC: Heating, ventilation and air conditioningHeating devices, or systems: *Block heater, or headbolt heater, an electric heater that heats the engine of a car to ease starting in cold weather *Boiler *Cathode heater, a coil or… … Wikipedia
NYC Mohawk — The New York Central Railroad (NYC) called the 4 8 2 type of steam locomotive the Mohawk type. It was known as the Mountain type on other roads, but the mighty New York Central didn t see the name to be fitting on its famous Water Level Route, so … Wikipedia
NZR KA class — A streamlined KA class locomotive Power type Steam Builder NZR Hutt Workshops Build date 1939 1945, 1950 … Wikipedia
NZR KB class — Power type Steam Builder NZR Hillside Workshops, Dunedin Build date 1939 Configuration 4 8 4 Gauge 3 ft 6 in (1,067 mm) Cape gauge Whe … Wikipedia
Steam locomotive — A steam locomotive is a locomotive powered by steam. The term usually refers to its use on railways, but can also refer to a road locomotive such as a traction engine or steamroller.Steam locomotives dominated rail traction from the mid 19th… … Wikipedia