- Trickling filter
A trickling filter consists of a fixed bed of rocks,
gravel, slag, polyurethane foam, sphagnum peat moss, or plastic media over which sewageor other wastewaterflows downward and causes a layer or film of microbialslime to grow, covering the bed of media. Aerobicconditions are maintained by splashing, diffusion, and either by forced air flowing through the bed or natural convection of air if the filter medium is porous. The process mechanism, or how the removal of waste from the water happens, involves both absorptionand adsorptionof organic compoundswithin the sewage or other wastewater by the layer of microbial slime. Diffusion of the wastewater over the media furnishes dissolved air, the oxygenwhich the slime layer requires for the biochemical oxidationof the organic compounds and releases carbon dioxidegas, water and other oxidized end products. As the slime layer thickens, it becomes more difficult for air to penetrate the layer and an inner anaerobic layer is probably formed. This slime layer continues to build until it eventually sloughs off, breaking off longer growth into the treated effluentas a sludge that requires subsequent removal and disposal. Typically, a trickling filter is followed by a clarifier or sedimentation tank for the separation and removal of the sloughing. Other filters utilizing higher-density media such as sand, foam and peat moss do not produce a sludge that must be removed, but require forced air blowers and backwashing or an enclosed anaerobic environment.
The terms trickle filter, trickling biofilter, biofilter, biological filter and biological trickling filter are often used to refer to a trickling filter.
These systems have also been described as roughing filters, intermittent filters, packed media bed filters, alternative septic systems, percolating filters, attached growth processes, and fixed film processes.
The treatment of sewage or other wastewater with trickling filters is among the oldest and most well characterized treatment technologies.
The three basic types of trickle filters are used for:
* the treatment of small individual residential or rural sewage
* large centralized systems for treatment of municipal sewage
* systems applied to the treatment of industrial wastewater.
eptic system leach field
This is the simplest form of waste liquid disposal system, typically using pipes buried in loose sand or gravel to dissipate the liquid outflow from a
septic tank. Liquid purification is performed by a biofilmwhich naturally forms as a coating on the sand and gravel in the absorption field and feeds on the dissolved nutrients in the waste stream.
Due to the system being completely buried and generally isolated from the surface environment, the process of waste breakdown is slow and requires a relatively large surface area to absorb and process liquid wastes. If too much liquid wastes enter the field too quickly, the wastes may pass out of the biofilm before waste consumption can occur, leading to pollution of groundwater.
In order to prolong the life of a leaching field, one method of construction is to build two fields of piping side-by-side, and use a rotating flow valve to direct waste into one field at a time, switching between fields every year or two. This allows a period of rest to let the microorganisms have time to break down the wastes built up in the gravel bed.
In areas where the ground is insufficiently absorptive (fails the
percolation test) a homeowner may be required to construct a mound systemwhich is a special engineered waste disposal bed of sand and gravel mounded on the surface of the ground with poor liquids absorption.
Leach field dosing
Generally it is better if the biofilm is permitted a period of time to rest between liquid influxes and for the liquids to be evenly distributed through the leaching bed to promote biofilm growth throughout the pipe network. Typically flows from septic systems are either small surges (handwashing) or very large surges (clothes washer emptying), resulting in highly erratic liquid outflow into the field and uneven biofilm growth concentrating primarily around the field inlet and dropping off in the outer reaches of the piping system.
For this reason it is common for engineered mound systems to include an electrically powered "dosing system" which consists of a large capacity underground storage tank and lift pump after the septic tank. When the tank fills to a predetermined level, it is emptied into the leaching field.
The storage tank collects small outflows such as from handwashing and saves them for dosing when the tank fills from other sources. During this fill period the field is able to rest continuously. When full, the discharge dose fills out the entire field completely to the same degree of flow, every time, promoting an even biofilm growth throughout the system.
Dosing systems have maintenance requirements over traditional non-powered surge systems. The pump and float system can break down and require replacement, and the dosing system also needs electricity. However, the system can be designed so that in the event of power failure the storage tank overflows to the field operating in the traditional surge-flow manner until power is restored or repairs can be done.
oil Compaction issues
The biofilm is most productive if the absorption field is loosely packed, to permit easy air infiltration down into the biofilm bed. Consequently the land over the leaching field is often a restricted area where large vehicles cannot be allowed to drive, because the heavy weight will compact the bed, and potentially cause system failure due to hindering of biofilm growth.
One method to help prevent compaction of the field is to place a U-shaped cover over gravel trenches in the bed, with a dosing pipe suspended above the bed by the cover. Any weight from above is passed to the sides of the trench keeping the bed directly under the cover free from compaction.
ewage treatment trickle filters
Onsite sewage facilities(OSSF) are recognized as viable, low-cost, long-term, decentralizedapproaches to sewage treatment if they are planned, designed, installed, operated and maintained properly (USEPA, 1997). Sewage trickling filters are used in areas not serviced by municipal wastewater treatment plants (WWTP). They are typically installed in areas where the traditional septic tanksystem are failing, cannot be installed due to site limitations, or where improved levels of treatment are required for environmental benefits such as preventing contamination of ground wateror surface water.
Sites with a high
water table, high bedrock, heavy clay, small land area, or which require minimal site destruction (for example, tree removal) are ideally suited for trickling filters.
All varieties of sewage trickling filters have a low and sometimes intermittent power consumption. They can be somewhat more expensive than traditional septic tank-leach field systems, however their use allows for better treatment, a reduction in size of disposal area, less excavation, and higher density land development.
Configurations and components
All sewage trickling filter systems share the same fundamental
* a septic tank for fermentation and primary settling of solids
* a filter medium upon which beneficial
microbes(biomass, biofilm) are promoted and developed
* a container which houses the filter medium
* a distribution system for applying wastewater to be treated to the filter medium
* a distribution system for disposal of the treated effluent or percolation ponds.
By treating septic tank effluent before it is distributed into the ground, higher treatment levels are obtained and smaller disposal means such as
leach field, shallow pressure trench or area beds are required.
Systems can be configured for single-pass use where the treated water is applied to the trickling filter once before being disposed of, or for multi-pass use where a portion of the treated water is cycled back to the septic tank and re-treated via a
closed-loop. Multi-pass systems result in higher treatment quality and assist in removing Total Nitrogen (TN) levels by promoting nitrificationin the aerobic media bed and denitrificationin the anaerobic septic tank.
Trickling filters differ primarily in the type of filter media used to house the microbial colonies. Types of media most commonly used include plastic matrix material, open-cell
polyurethane foam, sphagnum peat moss, recycled tires, clinker, gravel, sandand geotextiles. Ideal filter medium optimizes surface areafor microbial attachment, wastewater retention time, allows air flow, resists plugging and does not degrade. Some residential systems require forced aeration units which will increase maintenance and operational costs.
Third-party verificationof trickling filters has proven them to be a reliable alternative to septic systems with increased levels of treatment performance and nitrogenremoval. Typical effluentquality parameters are Biochemical Oxygen Demand(BOD), Total suspended solids(TSS), Total Kjeldahl Nitrogen(TKN), and fecal coliforms.
The leading testing facility in the
United Statesis the MassachusettsAlternative Septic System Test Center, a program of the Buzzards Bay National Estuary Program. Testing conducted here includes the stringent Environmental Technology Initiative (ETI) where systems are tested in triplicate over two years, and the Environmental Technology Verification (ETV) program which is funded by the U.S. Environmental Protection Agency(EPA) and includes stress testing as well as evaluation of nitrogenremoval over 14 months. Systems are approved for installation by local, state and federal regulationsand controls.
Industrial wastewater treatment trickle filters
Wastewaters from a variety of industrial processes have been treated in trickling filters. Such industrial wastewater trickling filters consist of two types:
* Large tanks or concrete enclosures filled with plastic packing or other media. [ [http://faculty.kfupm.edu.sa/CE/msaleh/ChE%20107.11March06.ppt King Fahd University of Petroleum and Minerals, Course ChE 101.11] Saudi Aramco Engineering Development Program, pages 62-65 including Figure 11]
* Vertical towers filled with plastic packing or other media. [ [http://www.google.com/patents?hl=en&lr=&vid=USPAT4351729&id=U3c8AAAAEBAJ&oi=fnd&dq=trickle+filter+%22packed+tower%22+wastewater Biological filter and process] U.S. patent 4,351,729, September 28, 1982, Assigned to Celanese Corporation] [ [http://www.ag.auburn.edu/~davisda/classes/facilities/presentations/Recirc_overview.pdf Lecture] by Dr. Allen Davis,
Auburn University, page 6 of 8 pdf pages including schematic of packed tower trickling filter)]
The availability of inexpensive plastic tower packings has led to their use as trickling filter beds in tall towers, some as high as 20 meters.cite book|author=Beychok, Milton R. |title=
Aqueous Wastes from Petroleum and Petrochemical Plants| edition=1st Edition| publisher=John Wiley & Sons Ltd|year=1967|id=LCCN 67019834] As early as the 1960s, such towers were in use at: the Great Northern Oil's Pine Bend Refineryin Minnesota; the Cities Service Oil Company Trafalgar Refinery in Oakville, Ontarioand at a kraft paper mill. [E.H. Bryan and D.H. Moeller, "Aerobic Biological Oxidation Using Dowpac", Paper 42, Conference on Biological Waste Treatment, Manhattan College, April 20, 1960. [http://cobweb.ecn.purdue.edu/~alleman] ]
The treated water effluent from industrial wastewater trickling filters is very often subsequently processed in a clarifier-settler to remove the sludge that sloughs off the microbial slime layer attached to the trickling filter media (see Image 1 above).
Currently, some of the latest trickle filter technology involves aerated biofilters which are essentially trickle filters consisting of plastic media in vessels using blowers to inject air at the bottom of the vessels, with either downflow or upflow of the wastewater. [cite book|author=Marcus Van Sperling|title= Activated Sludge and Aerobic Biofilm Reactors|edition= |publisher =IWA Publications|year=2007|id=ISBN 1-84339-165-1]
Many countries regulate the composition of treated water effluents from industrial facilities. For example, in the United States, the
Clean Water Actmandates a National Pollutant Discharge Elimination System ( NPDES), which regulates industrial point sources that discharge pollutants into rivers, lakes, and oceans. All U.S. industrial facilities that discharge liquid effluents must obtain effluent discharge permits under that system.
Rotating biological contactors
Industrial wastewater treatment
* [http://web.deu.edu.tr/atiksu/ana52/atgrow.ppt Overview of Biological Wastewater Treatment]
* [http://web.deu.edu.tr/atiksu/ana52/ani4041.html The History of Fixed-Film Wastewater Treatment Systems]
Wikimedia Foundation. 2010.
Look at other dictionaries:
trickling filter — biologinis filtras statusas T sritis ekologija ir aplinkotyra apibrėžtis Biologinio nuotekų valymo įrenginio filtravimo laikmuo iš skaldos, keramzito, plastiko granulių. Nuotekas valo laikmens paviršiuje susidariusi biologinė plėvelė iš aerobinių … Ekologijos terminų aiškinamasis žodynas
trickling filter — A bed of rocks covered with a microbial film that aerobically degrades organic waste during secondary sewage treatment … Dictionary of microbiology
trickling filter — noun : an artificial bed of broken rock or other coarse material through which sewage or industrial wastes trickle after being sprayed on intermittently so that organic matter present is oxidized and removed by biological growths formed on the… … Useful english dictionary
filter-bottom block — noun : a hollow vitrified salt glazed clay block used in the floors of trickling filters in sewage treatment plants … Useful english dictionary
biological filter — biologinis filtras statusas T sritis ekologija ir aplinkotyra apibrėžtis Biologinio nuotekų valymo įrenginio filtravimo laikmuo iš skaldos, keramzito, plastiko granulių. Nuotekas valo laikmens paviršiuje susidariusi biologinė plėvelė iš aerobinių … Ekologijos terminų aiškinamasis žodynas
percoling filter — biologinis filtras statusas T sritis ekologija ir aplinkotyra apibrėžtis Biologinio nuotekų valymo įrenginio filtravimo laikmuo iš skaldos, keramzito, plastiko granulių. Nuotekas valo laikmens paviršiuje susidariusi biologinė plėvelė iš aerobinių … Ekologijos terminų aiškinamasis žodynas
percolating filter — noun : trickling filter … Useful english dictionary
Industrial wastewater treatment — covers the mechanisms and processes used to treat waters that have been contaminated in some way by anthropogenic industrial or commercial activities prior to its release into the environment or its re use.Most industries produce some wet waste… … Wikipedia
environmental works — ▪ civil engineering Introduction infrastructure that provides cities and towns with water supply, waste disposal, and pollution control services. They include extensive networks of reservoirs, pipelines, treatment systems, pumping stations … Universalium
Sewage treatment — The objective of sewage treatment is to produce a disposable effluent without causing harm to the surrounding environment, and also prevent pollution. Sewage treatment, or domestic wastewater treatment, is the process of removing contaminants… … Wikipedia