- Cutout (electric power distribution)
In the electrical distribution utility industry a cutout is a combination fuse and switch used in primary overhead feeder lines and taps to protect stepdown transformers from current surges and overloads.
A cutout consists of three major components:
*The cutout body, an open "C"-shaped frame that supports the "fuse holder" and a porcelain insulator that electrically isolates the conductive portions of the assembly from the support to which the insulator is fastened.
*The fuse holder, often called the "fuse tube" or "door", which contains the interchangeable fuse element and also acts as a simple knife switch. When the contained fuse operates or blows, the fuse holder will drop open, disengaging the knife switch, and hang from a hinge assembly. This hanging fuse holder provides a visible indication that the fuse has operated and assurance that the down-stream circuit is electrically isolated.
*The fuse element, or "fuse link", is the replaceable portion of the assembly that operates due to high electrical currents.
The fuse elements, or fuse links used in most distribution cutouts are
tinor silver alloy fuse links that melt (or operate) when exposed to high current conditions. Ampere ratings of fuse elements vary from 1 ampere to 200 amperes.
Cutouts are typically mounted about 20 degrees off vertical so that the center of gravity of the fuse holder is displaced and the fuse holder will rotate by its own weight and dangle when the fuse blows. Tension on the fuse link normally holds an ejector spring in a stable position. When the fuse blows, this tension is released which causes the ejector spring to rapidly pull the unmelted stub of the fuse link out of the fuse holder tube to reduce surge duration and damage to the transformer and fuse holder. This quenches any arc in the fuse holder.
Each fuse holder typically has an attached pull ring that can be hooked by a long fiberglass hookstick operated by a lineworker from the ground, to manually open the switch. While often used for switching, the standard cut out shown is not designed to be manually opened under load. For applications where the switch is likely to be used to interrupt power manually, a "load break" version is avaiable that has an attachment to quench the arc.
Up until the mid 1990s each manufacturer used their own dimensional standards for cutout design; by the late 1990s most cutouts were of an "interchangeable design." This design allows for the interchangeable use of cutout bodies and fuse holders manufactured by different vendors.
The fuse holder may be replaced by a couple of different kinds of "doors," including:
*a solid blade, which would allow the fuse holder assembly to be used as a switch only;
*a sectionalizer, which is an intelligent device that will allow one or more faults to occur before operating to interrupt the current.
* [http://www.google.com/patents?id=z9NjAAAAEBAJ&dq=1939371|U.S. Patent 1,939,371] — 1930 cutout with single hinge
* [http://www.google.com/patents?id=2ANtAAAAEBAJ&dq=2176227|U.S. Patent 2,176,227] — 1932 cutout with double hinge
* [http://www.google.com/patents?id=GFxZAAAAEBAJ&dq=2,519,289|U.S. Patent 2,519,289] — 1944 cutout with lightning arrestor inside the insulator
* [http://www.google.com/patents?id=m4AOAAAAEBAJ&dq=6,583,708|U.S. Patent 6,583,708] — recent cutout design
Wikimedia Foundation. 2010.
Look at other dictionaries:
Electric power distribution — … Wikipedia
Distribution transformer — Single phase distribution transformer in Canada A distribution transformer is a transformer that provides the final voltage transformation in the electric power distribution system, stepping down the voltage used in the distribution lines to the… … Wikipedia
Fuse cutout — Cutout (left) attached to a feeder line (connection at the right not shown). The lower wire goes to the transformer. In electrical distribution, a fuse cutout or cut out fuse is a combination of a fuse and a switch, used in primary overhead… … Wikipedia
Electricity distribution — is the penultimate stage in the delivery (before retail) of electricity to end users. It is generally considered to include medium voltage (less than 50 kV) power lines, electrical substations and pole mounted transformers, low voltage (less than … Wikipedia
Out of the Blue (Electric Light Orchestra album) — Out of the Blue Studio album by Electric Light Orchestra Released October 1977 … Wikipedia
Cut-out — may refer to: Cutout animation Cutout (electric power distribution), a combination fuse and knife switch used on power poles Cut out (espionage), a mechanism used to pass information Cut out (recording industry), deeply discounted or remaindered… … Wikipedia
Fuse (electrical) — A miniature time delay fuse used to protect electronic equipment, rated 0.3 amperes at 250 volts. 1.25 inches (about 32 mm) long … Wikipedia
Switch — For other uses, see Switch (disambiguation). Electrical switches. Top, left to right: circuit breaker, mercury switch, wafer switch, DIP switch, surface mount switch, reed switch. Bottom, left to right: wall switch (U.S. style), miniature toggle… … Wikipedia
printmaking — /print may king/, n. the art or technique of making prints, esp. as practiced in engraving, etching, drypoint, woodcut or serigraphy. [1925 30; PRINT + MAKING] * * * Art form consisting of the production of images, usually on paper but… … Universalium
printing — /prin ting/, n. 1. the art, process, or business of producing books, newspapers, etc., by impression from movable types, plates, etc. 2. the act of a person or thing that prints. 3. words, symbols, etc., in printed form. 4. printed material. 5.… … Universalium