- Boiler (steam generator)
A boiler or steam generator is a device used to create steam by applying heat energy to water. Although the definitions are somewhat flexible, it can be said that older steam generators were commonly termed boilers and worked at low to medium pressure (1–300 psi/0.069–20.684 bar; 6.895–2,068.427 kPa) but, at pressures above this, it is more usual to speak of a steam generator.
A boiler or steam generator is used wherever a source of steam is required. The form and size depends on the application: mobile steam engines such as steam locomotives, portable engines and steam-powered road vehicles typically use a smaller boiler that forms an integral part of the vehicle; stationary steam engines, industrial installations and power stations will usually have a larger separate steam generating facility connected to the point-of-use by piping. A notable exception is the steam-powered fireless locomotive, where separately-generated steam is transferred to a receiver (tank) on the locomotive.
Steam generator (component of prime mover)
The steam generator or boiler is an integral component of a steam engine when considered as a prime mover; however it needs be treated separately, as to some extent a variety of generator types can be combined with a variety of engine units. A boiler incorporates a firebox or furnace in order to burn the fuel and generate heat; the heat is initially transferred to water to make steam; this produces saturated steam at ebullition temperature saturated steam which can vary according to the pressure above the boiling water. The higher the furnace temperature, the faster the steam production. The saturated steam thus produced can then either be used immediately to produce power via a turbine and alternator, or else may be further superheated to a higher temperature; this notably reduces suspended water content making a given volume of steam produce more work and creates a greater temperature gradient in order to counter tendency to condensation due to pressure and heat drop resulting from work plus contact with the cooler walls of the steam passages and cylinders and wire-drawing effect from strangulation at the regulator. Any remaining heat in the combustion gases can then either be evacuated or made to pass through an economiser, the role of which is to warm the feed water before it reaches the boiler.
Haycock and wagon top boilers
For the first Newcomen engine of 1712, the boiler was little more than large brewer’s kettle installed beneath the power cylinder. Because the engine’s power was derived from the vacuum produced by condensation of the steam, the requirement was for large volumes of steam at very low pressure hardly more than 1 psi (6.9 kPa) The whole boiler was set into brickwork which retained some heat. A voluminous coal fire was lit on a grate beneath the slightly dished pan which gave a very small heating surface; there was therefore a great deal of heat wasted up the chimney. In later models, notably by John Smeaton, heating surface was considerably increased by making the gases heat the boiler sides, passing through a flue. Smeaton further lengthened the path of the gases by means of a spiral labyrinth flue beneath the boiler. These under-fired boilers were used in various forms throughout the 18th Century. Some were of round section (haycock). A longer version on a rectangular plan was developed around 1775 by Boulton and Watt (wagon top boiler). This is what is today known as a three-pass boiler, the fire heating the underside, the gases then passing through a central square-section tubular flue and finally around the boiler sides.
Cylindrical fire-tube boiler
An early proponent of the cylindrical form, was the American engineer, Oliver Evans who rightly recognised that the cylindrical form was the best from the point of view of mechanical resistance and towards the end of the 18th Century began to incorporate it into his projects. Probably inspired by the writings on Leupold’s “high-pressure” engine scheme that appeared in encyclopaedic works from 1725, Evans favoured “strong steam” i.e. non condensing engines in which the steam pressure alone drove the piston and was then exhausted to atmosphere. The advantage of strong steam as he saw it was that more work could be done by smaller volumes of steam; this enabled all the components to be reduced in size and engines could be adapted to transport and small installations. To this end he developed a long cylindrical wrought iron horizontal boiler into which was incorporated a single fire tube, at one end of which was placed the fire grate. The gas flow was then reversed into a passage or flue beneath the boiler barrel, then divided to return through side flues to join again at the chimney (Columbian engine boiler). Evans incorporated his cylindrical boiler into several engines, both stationary and mobile. Due to space and weight considerations the latter were one-pass exhausting directly from fire tube to chimney. Another proponent of “strong steam” at that time was the Cornishman, Richard Trevithick. His boilers worked at 40–50 psi (276–345 kPa) and were at first of hemispherical then cylindrical form. From 1804 onwards Trevithick produced a small two-pass or return flue boiler for semi-portable and locomotive engines. The Cornish boiler developed around 1812 by Richard Trevithick was both stronger and more efficient than the simple boilers which preceded it. It consisted of a cylindrical water tank around 27 feet (8.2 m) long and 7 feet (2.1 m) in diameter, and had a coal fire grate placed at one end of a single cylindrical tube about three feet wide which passed longitudinally inside the tank. The fire was tended from one end and the hot gases from it travelled along the tube and out of the other end, to be circulated back along flues running along the outside then a third time beneath the boiler barrel before being expelled into a chimney. This was later improved upon by another 3-pass boiler, the Lancashire boiler which had a pair of furnaces in separate tubes side-by-side. This was an important improvement since each furnace could be stoked at different times, allowing one to be cleaned while the other was operating.
Railway locomotive boilers were usually of the 1-pass type, although in early days, 2-pass "return flue" boilers were common, especially with locomotives built by Timothy Hackworth.
A significant step forward came in France in 1828 when Marc Seguin devised a two-pass boiler of which the second pass was formed by a bundle of multiple tubes. A similar design with natural induction used for marine purposes was the popular “Scotch” marine boiler.
Prior to the Rainhill trials of 1829 Henry Booth, treasurer of the Liverpool and Manchester Railway suggested to George Stephenson, a scheme for a multi-tube one-pass horizontal boiler made up of two units: a firebox surrounded by water spaces and a boiler barrel consisting of two telescopic rings inside which were mounted 25 copper tubes; the tube bundle occupied much of the water space in the barrel and vastly improved heat transfer. Old George immediately communicated the scheme to his son Robert and this was the boiler used on Stephenson's Rocket, outright winner of the trial. The design was and formed the basis for all subsequent Stephensonian-built locomotives, being immediately taken up by other constructors; this pattern of fire-tube boiler has been built ever since.
The 1712 boiler was assembled from riveted copper plates with a domed top made of lead in the first examples. Later boilers were made of small wrought iron plates riveted together. The problem was producing big enough plates, so that even pressures of around 50 psi (344.7 kPa) were not absolutely safe, nor was the cast iron hemispherical boiler initially used by Richard Trevithick. This construction with small plates persisted until the 1820s, when larger plates became feasible and could be rolled into a cylindrical form with just one butt-jointed seam reinforced by a gusset; Timothy Hackworth's Sans Pareil 11 of 1849 had a longitudinal welded seam. Welded construction for locomotive boilers was extremely slow to take hold.
Once-through monotubular water tube boilers as used by Doble, Lamont and Pritchard are capable of withstanding considerable pressure and of releasing it without danger of explosion.
The source of heat for a boiler is combustion of any of several fuels, such as wood, coal, oil, or natural gas. Nuclear fission is also used as a heat source for generating steam. Heat recovery steam generators (HRSGs) use the heat rejected from other processes such as gas turbines.
Solid fuel firing
In order to improve the burning characteristics of the fire, air needs to be supplied through the grate, or more importantly above the fire. Most boilers now depend on mechanical draft equipment rather than natural draught. This is because natural draught is subject to outside air conditions and temperature of flue gases leaving the furnace, as well as chimney height. All these factors make effective draught hard to attain and therefore make mechanical draught equipment much more economical. There are three types of mechanical draught:
- Induced draught: This is obtained one of three ways, the first being the "stack effect" of a heated chimney, in which the flue gas is less dense than the ambient air surrounding the boiler. The denser column of ambient air forces combustion air into and through the boiler. The second method is through use of a steam jet. The steam jet or ejector oriented in the direction of flue gas flow induces flue gases into the stack and allows for a greater flue gas velocity increasing the overall draught in the furnace. This method was common on steam driven locomotives which could not have tall chimneys. The third method is by simply using an induced draught fan (ID fan) which sucks flue gases out of the furnace and up the stack. Almost all induced draught furnaces have a negative pressure.
- Forced draught: draught is obtained by forcing air into the furnace by means of a fan (FD fan) and ductwork. Air is often passed through an air heater; which, as the name suggests, heats the air going into the furnace in order to increase the overall efficiency of the boiler. Dampers are used to control the quantity of air admitted to the furnace. Forced draught furnaces usually have a positive pressure.
- Balanced draught: Balanced draught is obtained through use of both induced and forced draft. This is more common with larger boilers where the flue gases have to travel a long distance through many boiler passes. The induced draft fan works in conjunction with the forced draft fan allowing the furnace pressure to be maintained slightly below atmospheric.
The next stage in the process is to boil water and make steam. The goal is to make the heat flow as completely as possible from the heat source to the water. The water is confined in a restricted space heated by the fire. The steam produced has lower density than the water and therefore will accumulate at the highest level in the vessel; its temperature will remain at boiling point and will only increase as pressure increases. Steam in this state (in equilibrium with the liquid water which is being evaporated within the boiler) is named "saturated steam". For example, saturated steam at atmospheric pressure boils at 100 °C (212 °F). Saturated steam taken from the boiler may contain entrained water droplets, however a well designed boiler will supply virtually "dry" saturated steam, with very little entrained water. Continued heating of the saturated steam will bring the steam to a "superheated" state, where the steam is heated to a temperature above the saturation temperature, and no liquid water can exist under this condition. Most reciprocating steam engines of the 19th century used saturated steam, however modern steam power plants universally use superheated steam which allows higher steam cycle efficiency.
L.D. Porta gives the following equation determining the efficiency of a steam locomotive, applicable to steam engines of all kinds: power (kW) = steam Production (kg h−1)/Specific steam consumption (kg/kW h).
A greater quantity of steam can be generated from a given quantity of water by superheating it. As the fire is burning at a much higher temperature than the saturated steam it produces, far more heat can be transferred to the once-formed steam by superheating it and turning the water droplets suspended therein into more steam and greatly reducing water consumption.
The superheater works like coils on an air conditioning unit, however to a different end. The steam piping (with steam flowing through it) is directed through the flue gas path in the boiler furnace. This area typically is between 1300–1600 degrees Celsius (2372–2912 °F). Some superheaters are radiant type (absorb heat by thermal radiation), others are convection type (absorb heat via a fluid i.e. gas) and some are a combination of the two. So whether by convection or radiation the extreme heat in the boiler furnace/flue gas path will also heat the superheater steam piping and the steam within as well. It is important to note that while the temperature of the steam in the superheater is raised, the pressure of the steam is not: the turbine or moving pistons offer a "continuously expanding space" and the pressure remains the same as that of the boiler. The process of superheating steam is most importantly designed to remove all droplets entrained in the steam to prevent damage to the turbine blading and/or associated piping. Superheating the steam expands the volume of steam, which allows a given quantity (by weight) of steam to generate more power.
When the totality of the droplets are eliminated, the steam is said to be in a superheated state.
In a Stephensonian firetube locomotive boiler, this entails routing the saturated steam through small diameter pipes suspended inside large diameter firetubes putting them in contact with the hot gases exiting the firebox; the saturated steam flows backwards from the wet header towards the firebox, then forwards again to the dry header. Superheating only began to be generally adopted for locomotives around the year 1900 due to problems of overheating of and lubrication of the moving parts in the cylinders and steam chests. Many firetube boilers heat water until it boils, and then the steam is used at saturation temperature in other words the temperature of the boiling point of water at a given pressure (saturated steam); this still contains a large proportion of water in suspension. Saturated steam can and has been directly used by an engine, but as the suspended water cannot expand and do work and work implies temperature drop, much of the working fluid is wasted along with the fuel expended to produced it.
Water tube boiler
Another way to rapidly produce steam is to feed the water under pressure into a tube or tubes surrounded by the combustion gases. The earliest example of this was developed by Goldsworthy Gurney in the late 1820s for use in steam road carriages. This boiler was ultra-compact and light in weight and this arrangement has since become the norm for marine and stationary applications. The tubes frequently have a large number of bends and sometimes fins to maximize the surface area. This type of boiler is generally preferred in high pressure applications since the high pressure water/steam is contained within narrow pipes which can contain the pressure with a thinner wall. It can however be susceptible to damage by vibration in surface transport appliances. In a cast iron sectional boiler, sometimes called a "pork chop boiler" the water is contained inside cast iron sections. These sections are mechanically assembled on site to create the finished boiler.
High pressure water tube boilers generate steam rapidly at high temperatures that can be increased by lengthening the tubes. The superheater section of the tubes.
Supercritical steam generator
Supercritical steam generators are frequently used for the production of electric power. They operate at supercritical pressure. In contrast to a "subcritical boiler", a supercritical steam generator operates at such a high pressure (over 3,200 psi/22.06 MPa or 3,200 psi/220.6 bar) that actual boiling ceases to occur, the boiler has no liquid water - steam separation. There is no generation of steam bubbles within the water, because the pressure is above the critical pressure at which steam bubbles can form. It passes below the critical point as it does work in a high pressure turbine and enters the generator's condenser. This results in slightly less fuel use and therefore less greenhouse gas production. The term "boiler" should not be used for a supercritical pressure steam generator, as no "boiling" actually occurs in this device.
Feed water for boilers needs to be as pure as possible with a minimum of suspended solids and dissolved impurities which cause corrosion, foaming and water carryover. Various chemical treatments have been employed over the years, the most successful being Porta treatment. This contains a foam modifier that acts as a filtering blanket on the surface of the water that considerably purifies steam quality.
Many steam engines possess boilers that are pressure vessels that contain a great deal of potential energy. Steam explosions can and have caused great loss of life in the past. While variations in standards may exist in different countries, stringent legal, testing, training and certification is applied to try to minimise or prevent such occurrences.
Failure modes include:
- overpressurisation of the boiler
- insufficient water in the boiler causing overheating and vessel failure
- pressure vessel failure of the boiler due to inadequate construction or maintenance.
The Doble steam car uses a once-through type contra-flow generator, consisting of a continuous tube. The fire here is on top of the coil instead of underneath. Water is pumped into the tube at the bottom and the steam is drawn off at the top. This means that every particle of water and steam must necessarily pass through every part of the generator causing an intense circulation which prevents any sediment or scale from forming on the inside of the tube. Water enters the bottom of this tube at the flow rate of 600 feet (183 m) a second with less than two quarts of water in the tube at any one time.
As the hot gases pass down between the coils, they gradually cool, as the heat is being absorbed by the water. The last portion of the generator with which the gases come into contact remains the cold incoming water. The fire is positively cut off when the pressure reaches a pre-determined point, usually set at 750 psi (5.2 MPa), cold water pressure; a safety valve set at 1,200 lb (544 kg) provides added protection. The fire is automatically cut off by temperature as well as pressure, so in case the boiler were completely dry it would be impossible to damage the coil as the fire would be automatically cut off by the temperature .
Similar forced circulation generators, such as the Pritchard and Lamont and Velox boilers present the same advantages.
Essential boiler fittings
- Safety valve
- Pressure measurement
- Blowdown Valves
- Main steam Stop Valve
- Feed check valves
- Fusible Plug
- Water gauge
- Low-Water Alarm
- Low Water Fuel Cut-out
- Inspector's Test Pressure Gauge Attachment
- Name Plate
- Registration Plate
- Feedwater pump
- Safety valve: used to relieve pressure and prevent possible explosion of a boiler. As originally devised by Denis Papin it was a dead weight on the end of an arm that was lifted by excess steam pressure. This type of valve was used throughout the 19th century for stationary steam engines, however the vibrations of locomotive engines caused the valves to bounce and "fizzle" wasting steam. They were therefore replaced by various spring-loaded devices.
- Water column: to show the operator the level of fluid in the boiler, a water gauge or water column is provided
- Bottom blowdown valves
- Surface blowdown line
- Feed Pump(s)
- Circulating pump
- Check valve or clack valve: a non-return stop valve by which water enters the boiler.
- Main steam stop valve
- Steam traps
- Main steam stop/Check valve used on multiple boiler installations
- Fuel oil system
- Gas system
- Coal system
- Automatic combustion systems
Application of steam boilers
Steam boilers are used where steam and hot steam is needed. Hence, steam boilers are used as generators to produce electricity in the energy business. Besides many different application areas in the industry for example in heating systems or for cement production, steam boilers are used in agriculture as well for soil steaming.
- Glossary of boiler terminology
- Boiler – colloquial name for a hot water heater (in hydronics)
- Steam generator (nuclear power) – a heat exchanger in a pressurized water reactor -equipped nuclear power plant
- Steam generator (railroad) – a device used in trains to provide heat to passenger cars
- ^ Young, Robert: “Timothy Hackworth and the Locomotive”; the Book guild Ltd, Lewes, U.K. (2000) (reprint of 1923 ed.) p.326
- ^ Bell, A.M. (1952) Locomotives p 46. Virtue and Company Ltd, London
- ^ Walton J.N. (1965-74) Doble Steam Cars, Buses, Lorries, and Railcars . "Light Steam Power" Isle of Man, UK
Wikimedia Foundation. 2010.
См. также в других словарях:
Steam generator — A steam generator is a device used to boil water to create steam. It may refer to:*Boiler (steam generator), a closed vessel in which water is heated under pressure *Steam generator (nuclear power), a heat exchanger in a pressurized water reactor … Wikipedia
Steam generator (railroad) — Steam generator is the term used to describe a type of boiler used to produce steam for climate control and potable water heating in railroad passenger cars. The output of a railroad steam generator is low pressure, saturated steam that is passed … Wikipedia
steam generator — noun : a large apparatus for converting hot water into steam at high pressure and often with supplementary coils to superheat the steam * * * steam generator, a unit for producing high pressure steam, consisting of a combined boiler and… … Useful english dictionary
Boiler — For the Limp Bizkit song, see Boiler (song). A portable boiler (preserved, Poland) … Wikipedia
Steam engine — A steam engine is a heat engine that performs mechanical work using steam as its working fluid. [ [http://www.britannica.com/EBchecked/topic/564472/steam engine steam engine Britannica Online Encyclopedia ] ] Steam engines have a long history,… … Wikipedia
Steam car — Stanley Steam Car (1912) White touring car (1909) … Wikipedia
boiler — boilerless, adj. /boy leuhr/, n. 1. a closed vessel or arrangement of vessels and tubes, together with a furnace or other heat source, in which steam or other vapor is generated from water to drive turbines or engines, supply heat, process… … Universalium
Steam tricycle — A steam tricycle is a steam driven three wheeled vehicle.HistoryIn the early days of motorised vehicle development, a number of experimenters built steam powered vehicles with three wheels. The first steam tricycle – and probably the first true… … Wikipedia
boiler — noun Date: circa 1540 1. one that boils 2. a. a vessel used for boiling b. the part of a steam generator in which water is converted into steam and which consists usually of metal shells and tubes c. a tank in which water is heated or hot water… … New Collegiate Dictionary
Generator — Gen er*a tor, n. [L.] 1. One who, or that which, generates, begets, causes, or produces. [1913 Webster] 2. An apparatus in which vapor or gas is formed from a liquid or solid by means of heat or chemical process, as a steam boiler, gas retort, or … The Collaborative International Dictionary of English