- Split-phase electric power
A split phase
electricity distributionsystem is a 3-wire single-phasedistribution system, commonly used in North America for single-family residential and light commercial (up to about 100 kVA) applications. It is the AC equivalent of the original Edison 3-wire direct current system. Its primary advantage is that it saves conductor material over a single ended single phase system while only requiring single phase on the supply side of the distribution transformer. [Terrell Croft and Wilford Summers (ed), "American Electricians' Handbook, Eleventh Edition", McGraw Hill, New York (1987) ISBN 0-07-013932-6, chapter 3, pages 3-10, 3-14 to 3-22. ] Since there are two live conductors in the system, it is sometimes incorrectly referred to as " two phase". To avoid confusion with split-phase motor start applications, it is appropriate to call this power distribution system a 3-wire, single-phase, mid-point neutral system.
In North America, the
high leg deltasystem allows single-phase 120 V loads and 240 V three-phase loads both to be served by the same three-phase, four-wire distribution system.
transformersupplying a 3-wire distribution system has a single-phase input (primary) winding. The output (secondary) winding is center-tapped and the center tap connected to neutral. This 3-wire system is common in countries with a standard phase-neutral voltage of 120 V. In this case, the transformer voltage is 120 V on either side of the center tap, giving 240 V between the two live conductors.
Europe, 230/460 V, 3-wire, single-phasesystems are used to run farms and small groups of houses when only two of the three-phasehigh voltage conductors are available (it is cheaper to run two wires than three). Houses in the UK normally only have single-ended single-phase power and so (as with three-phase) only one active line and the neutral is taken to each house. In the case of a property with a larger demand it is usually split out at the intake point and treated as two totally separate installations since there is no need for 460 V final circuits, and standard consumer units (circuit breaker boxes), meters and distribution boards are designed around either three-phase or single-phase circuits.
In Australia and New Zealand, remote loads are connected to the grid using SWER (Single Wire Earth Return) transmission lines (it is cheaper to run one wire than two). The primary of the transformer is connected between the high voltage line and earth, the secondary is a 3-wire single-phase system as described here, the secondary voltage being 230/460 V. Single phase loads are split between the two circuits. Hot water services use both circuits.
In countries whose standard phase to neutral voltage is 120 V, lighting and small appliances are connected between a live wire and the neutral. Large appliances, such as cooking equipment, space heating, water
pumps, clothes dryers, and air conditioners are connected across the two live conductors and operate at 240 V, requiring less current and smaller conductors than would be needed if the appliances were designed for 120 V operation.
No individual conductor will be at more than 120 V potential with respect to ground (earth), reducing the earth
fault currentwhen compared to a 240 V, 2-wire system that has one leg (the neutral) earthed.
In the USA, the practice originated with the DC distribution system developed by
Thomas Edison. By dividing a lighting load into two equal groups of lamps connected in series, the total supply voltage can be doubled and the size of conductors cut in half if current carry capacity is determining cable size or by a quarter if cable voltage drop is the size determining factor. Since the load will vary as lamps are switched on and off, just connecting the groups in series would result in excessive voltage and brightness variation. By connecting the two lamp groups to a neutral, intermediate in potential between the two live legs, any imbalance of the load will be supplied by a current in the neutral, giving substantially constant voltage across both groups.
Split phase systems require less copper for the same voltage drop, final utilization voltage, and power transmitted than single phase systems. (Voltage drop tends to be the dominant design consideration in the sizing of long power distribution cable runs.) Just how much depends on the situation. However, the extra cores may require more insulation material and more complex processing, reducing the cost saving for lower power runs.
If the load were guaranteed to be balanced, then the neutral conductor would not carry any current (and so, would not be needed) and the system would be equivalent to a single ended system of twice the voltage with the live cables taking half the current. Assuming volt drop to be the dominant design consideration (as it tends to be for long cable runs at mains voltage) this system would use 25% of the copper of the equivalent single ended single phase system but would be wildly impractical for real varying loads. At the other extreme, if the system were designed to provide volt drop in spec when one side was fully loaded and the other completely unloaded the total copper required would be 75% of that required for a single end single phase circuit. In practice a measure between these extremes can be applied (commonly sizing the conductors for correct volt drop with a full balanced load and then making the neutral as big as the other two conductors).
A variation is the 240 V delta 4-wire system, also known as a high-leg or red-leg delta. This is a three-phase 240 V delta connected system, in which one winding of the transformer has a center tap which is connected to ground and used as the system neutral. This allows a single service to supply 120 V for lighting, 240 V single-phase for heating appliances, and 240 V three-phase for motor loads (such as air conditioning compressors). Two of the phases are 120 V to neutral, the third phase or "high leg" is 208 V to neutral.
Systems split more than two ways are technically possible with both AC and DC but have the significant disadvantage that no matter which point is tied to ground some of the wires will have a higher earth relative voltage than the utilisation voltage; therefore, such systems are not used in normal power distribution.
In the UK, electric tools and portable lighting at construction sites are sometimes fed from a centre-tapped system with only 55 V between live conductors and the earth. This system is used with 110 V equipment and therefore no neutral conductor is needed. The intention is to reduce the electrocution hazard that may exist when using electrical equipment at a wet or outdoor construction site. An incidental benefit is that the filaments of 110 V
incandescent lamps are thicker and therefore mechanically more rugged and shock-resistant than 230 V lamps.
Technical power (balanced power)
In a so-called "technical power" system, an isolation
transformerwith a center tap is used to create a separate supply with conductors at a balanced 60 volts with respect to ground. Unlike a three-wire distribution system, the grounded neutral is not distributed to the loads; only line-to-line connections at 120 volts are used. A balanced power system is only used for specialized distribution in audio and video production studios, sound and television broadcasting, and installations of sensitive scientific instruments. The purpose of a balanced power system is to minimize the noise coupled into sensitive equipment from the power supply. In the United States the National Electrical Codeprovides rules for such installations [NFPA 70, National Electrical Code 2005, National Fire Protection Association, Inc., Quincy, Massachusetts USA, (2005). no ISBN , article 640] . Technical power systems are not to be used for general-purpose lighting or other equipment, and may use special sockets to ensure only approved equipment is connected to the system.
A split-phase motor is a type of single-phase
electric motor. A split-phase motor runs on a single phase and has no special relationship to a split-phase (3-wire) distribution system.
Wikimedia Foundation. 2010.
Look at other dictionaries:
Single-phase electric power — In electrical engineering, single phase electric power refers to the distribution of alternating current electric power using a system in which all the voltages of the supply vary in unison. Single phase distribution is used when loads are mostly … Wikipedia
Three-phase electric power — This article deals with where, how and why three phase is used. For information on the basic mathematics and principles of three phase, see three phase. Three phase electric power is a common method of alternating current electric power… … Wikipedia
Two-phase electric power — Two phase electrical power was an early 20th century polyphase alternating current electric power distribution system. Two circuits were used, with voltage phases differing by 90 degrees. Usually circuits used four wires, two for each phase. Less … Wikipedia
Electric power distribution — … Wikipedia
Power engineering — Power engineering, also called power systems engineering, is a subfield of electrical engineering that deals with the generation, transmission and distribution of electric power as well as the electrical devices connected to such systems… … Wikipedia
Electric motor — For other kinds of motors, see motor (disambiguation). For a railroad electric engine, see electric locomotive. Various electric motors. A 9 volt PP3 transistor battery is in the center foreground for size comparison. An electric motor converts… … Wikipedia
electric motor — motor (def. 4). [1885 90] * * * Introduction any of a class of devices that convert electrical energy to mechanical energy, usually by employing electromagnetic phenomena. Most electric motors develop their mechanical torque by the… … Universalium
Power dividers and directional couplers — A 10 dB 1.7–2.2 GHz directional coupler. From left to right: input, coupled, isolated (terminated with a load), and transmitted port … Wikipedia
Phase-shift keying — Passband modulation v · d · e Analog modulation AM · … Wikipedia
Electric vehicle battery — Further information: Rechargeable electricity storage system For the starting, lighting and ignition system battery of an automobile, see Automotive battery. A Mitsubishi i MiEV having its batteries installed in Japan … Wikipedia