- Two-phase electric power
Two-phase electrical power was an early 20th century polyphase
alternating currentelectric power distribution system. Two circuits were used, with voltage phases differing by 90 degrees. Usually circuits used four wires, two for each phase. Less frequently, three wires were used, with a common wire with a larger-diameter conductor. Some early two-phase generators had two complete rotor and field assemblies, with windings physically offset by 90 electrical degrees to provide two-phase power. The generatorsat Niagara Fallsinstalled in 1895 were the largest generators in the world at the time and were two-phase machines.
The advantage of two-phase electrical power was that it allowed for simple, self-starting electric motors. In the early days of
electrical engineering, it was easier to analyze and design two-phase systems where the phases were completely separated. [ Thomas J. Blalock "The first polyphase system - a look back at two-phase power for ac distribution", in " IEEE Power and Energy Magazine",March-April 2004, ISSN 1540-7977 pg. 63 ] It was not until the invention of the method of symmetrical componentsin 1918 that polyphase power systems had a convenient mathematical tool for describing unbalanced load cases. The revolving magnetic field produced with a two-phase system allowed electric motors to provide torquefrom zero motor speed, which was not possible with a single-phase induction motor(without extra starting means). Induction motors designed for two-phase operation use the same winding configuration as capacitor start single-phase motors. Three-phase electric powerrequires less conductor mass for the same voltage and overall amount of power, compared with a two-phase four-wire circuit of the same carrying capacity. [ Terrell Croft and Wilford Summers (ed), "American Electricans' Handbook, Eleventh Edition", McGraw Hill, New York (1987) ISBN 0-07-013932-6 page 3-10, figure 3-23 ] It has all but replaced two-phase power for commercial distribution of electrical energy, but two-phase circuits are still found in certain control systems.
Two-phase circuits typically use two separate pairs of current-carrying conductors. Alternatively, three wires may be used, but the common conductor carries the vector sum of the phase currents, which requires a larger conductor. Three phase can share conductors so that the three phases can be carried on three conductors of the same size. In electrical power distribution, a requirement of only three conductors rather than four represented a considerable distribution-wire cost savings due to the expense of conductors and installation.
Two-phase power can be derived from a three-phase source using two
transformers in a Scott connection. One transformer primary is connected across two phases of the supply. The second transformer is connected to a center-tap of the first transformer, and is wound for 86.6% of the phase-to-phase voltage on the 3-phase system. The secondaries of the transformers will have two phases 90 degrees apart in time, and a balanced two-phase load will be evenly balanced over the three supply phases.
Three-wire, 120/240 volt single phase power used in the USA and Canada is sometimes incorrectly called "two-phase". The proper term is "
split phase" or "3-wire single-phase".
*Donald G. Fink and H. Wayne Beaty, "Standard Handbook for Electrical Engineers, Eleventh Edition",McGraw-Hill, New York, 1978, ISBN 0-07-020974-X
* Edwin J. Houston and Arthur Kennelly, "Recent Types of Dynamo-Electric Machinery", copyright American Technical Book Company 1897, published by P.F. Collier and Sons New York, 1902
Wikimedia Foundation. 2010.
Look at other dictionaries:
Three-phase electric power — This article deals with where, how and why three phase is used. For information on the basic mathematics and principles of three phase, see three phase. Three phase electric power is a common method of alternating current electric power… … Wikipedia
Single-phase electric power — In electrical engineering, single phase electric power refers to the distribution of alternating current electric power using a system in which all the voltages of the supply vary in unison. Single phase distribution is used when loads are mostly … Wikipedia
Split-phase electric power — A split phase electricity distribution system is a 3 wire single phase distribution system, commonly used in North America for single family residential and light commercial (up to about 100 kVA) applications. It is the AC equivalent of the… … Wikipedia
Electric power transmission — Electric transmission redirects here. For vehicle transmissions, see diesel electric transmission. 400 kV high tension transmission lines near Madrid Electric power transmission or high voltage electric transmission is the bulk transfer of… … Wikipedia
Electric power distribution — … Wikipedia
Electric power — is defined as the rate at which electrical energy is transferred by an electric circuit. The SI unit of power is the watt.When electric current flows in a circuit, it can transfer energy to do mechanical or thermodynamic work. Devices convert… … Wikipedia
Dynamic demand (electric power) — Dynamic Demand is the name of a semi passive technology for adjusting load demands on an electrical power grid. (It is also the name of an independent not for profit organization in the UK supported by a charitable grant from the Esmée Fairbairn… … Wikipedia
Power engineering — Power engineering, also called power systems engineering, is a subfield of electrical engineering that deals with the generation, transmission and distribution of electric power as well as the electrical devices connected to such systems… … Wikipedia
Power outage — A power outage (also known as power cut , power failure , power loss , or blackout ) is the loss of the electricity supply to an area.The reasons for a power failure can for instance be a defect in a power station, damage to a power line or other … Wikipedia
Electric locomotive — Electric Trains redirects here. For the 1995 Squeeze single, see Electric Trains (song). An electric locomotive is a locomotive powered by electricity from an external source. Sources include overhead lines, third rail or an on board electricity… … Wikipedia