- Arc-fault circuit interrupter
An arc fault circuit interrupter (AFCI) is a
circuit breakerdesigned to prevent fires by detecting non-working electrical arcs and disconnect power before the arc starts a fire. The AFCI should distinguish between a working arc that may occur in the brushes of a vacuum sweeper, light switch, or other household devices and a non-working arc that can occur, for instance, in a lamp cord that has a broken conductor in the cord from overuse. Arc faults in a home are one of the leading causes for household fires.
AFCIs resemble a GFCI/RCD (Ground-Fault Circuit Interrupt/Residual-Current Device) in that they both have a test button, though it is important to distinguish between the two. GFCIs are designed to protect against electrical shock, while AFCIs are primarily designed to protect against fire.
Electrical Code Requirements
Starting with the 1999 version of the
National Electrical Code(NEC, also called NFPA 70) in the United States and the 2002 version of the Canadian Electrical Codein Canada(CSA Standard C22.1), the national codes require AFCIs in all circuits that feed receptacles in bedrooms of dwelling units. This requirement is typically accomplished by using a kind of circuit-breaker (defined by UL 1699) in the breaker panelthat provides combined arc-fault and overcurrentprotection. The AFCI requirements of the NEC have not been adopted as written by all U.S.A. jurisdictions.
The AFCI is intended to prevent fire from arcs. AFCI circuit breakers are designed to meet one of two standards as specified by UL 1699: "branch" type or "combination" type (note: the Canadian Electrical Code uses different terminology but similar technical requirements). A branch type AFCI trips on 75 Amperes of arcing current from the line wire to either the neutral or ground wire. A combination type adds series arcing detection to branch type performance. Combination type AFCIs trip on 5 Amperes of series arcing. Advanced
electronicsinside an AFCI breaker detect sudden bursts of electrical currentin milliseconds, long before a standard circuit breakeror fuse would trip. A "combination AFCI breaker" will provide protection against
# Parallel arcing (line to neutral).
# Series arcing (a loose, broken, or otherwise high resistance segment in a single line)
# Ground arcing (from line, or neutral, to ground)
# Overload protection
# Short circuit protection
In 2002, the NEC removed the word "receptacle" leaving "outlets", in effect adding lights within dwelling bedrooms to the requirement [debated interpretation] . The 2005 code made it more clear that all outlets must be protected, despite code making panel discussion about excluding bedroom smoke detectors from the requirement. "Outlets" is defined in "Article 100 Definitions" of the NEC as "A point on the wiring system where current is taken to supply utilization equipment" and this includes receptacles, light fixtures, and smoke alarms, among other things.
Beginning January 2008, only "combination type" AFCIs will meet the NEC requirement. The 2008 NEC requires installation of combination-type AFCIs in all 15 and 20 amp residential circuits with the exception of laundries, kitchens, bathrooms, and garage, and unfinished basements.
month = October
day = 8
year = 2008
time = 17:14
timestamp = 20081008171442
AFCIs are designed to protect against fires caused by electrical arcing faults. However, they provide no specific protection against "glowing" connections, excess current, high line voltages, or low line voltages. For descriptions of electrical fire causes, see "How Electricity Starts Fires", John S Robison, P.E., Electrical Line magazine, November / December 2007 issue, pages 60-70 (http://www.electricalline.com/); NFPA 921 "Guide for Fire and Explosion Investigations", 2004 edition; and "Ignition Handbook", Dr. Vytenis Babrauskas, Fire Science Publishers, 2003.
Glowing connections occur when relatively high
electric currentexists in a relatively large resistance. Heat comes from power dissipation. Power (in Watts, abbreviated W) equals the current (in Amperes, abbreviated Amps or A) multiplied by the current (in Amperes) multiplied by the resistance (in Ohms). For example, a 60 Watt lamp operating on a 120 V circuit draws 1/2 Ampere of current. An 1800 Watt space heater on a 120 V circuit draws up to 15 Amperes. If a bad wiring junction in a circuit has a resistance of 1 Ohm, then a 60 W lamp will cause it to dissipate 0.25 Watt of power (0.5 A * 0.5 A * 1 Ohm). In contrast, an 1800 W heater could theoretically cause the bad wiring junction to dissipate 178 Watts (13 A * 13 A * 1 Ohm). Note that the current is less than 15 A because of the combined resistance of the heater plus the bad wiring junction. This heat dissipated in a small junction area can generate over 1000 degrees C of heat. That amount of heat can ignite most flammable materials. Bad wiring junctions can occur in utilization equipment, cords, or premise wiring (especially in defective switch, socket, plug, or wire connection, even at circuit breaker or fuse panels). High resistance junctions are commonly observed in improperly terminated aluminum wirejunctions. No technology located in a circuit breaker or fuse panel could detect a high-resistance wiring fault as there is no measurable characteristic to distinguish a glow fault from the normal operation of a branch circuit. Power Fault Circuit Interrupters (PFCI) located in receptacles are designed to prevent fires caused by glowing connections in premise wiring or panels. From the receptacle, a PFCI can detect the voltage drop when high current rxists in a high resistance junction. In a properly designed circuit, substantial voltage drops should never occur. Proper wire terminations inside utilization equipment (e.g. appliances, lamps, heaters) and cords prevent high-resistance connections that can lead to fires.
Excess current can heat entire lengths of wire. Thermal circuit breakers are designed to protect against excess current through the premise circuit wiring. However, excess current through the smaller gauge wires in utilization equipment can exist, at levels below the trip thresholds of a circuit breaker. Overload Fault Circuit Interrupters (OFCI) are designed to protect against excess current into utilization equipment. OFCIs must be located within receptacles. Both thermal circuit breakers and OFCIs are required to prevent fire ignition from excess current.
High line-voltage creates excess power and heat in utilization devices such as heaters, light bulbs, appliances, motors, and electronics. In extreme cases, this heat can ignite fires. One extreme source of high line voltage occurs from a neutral path opening within a two-leg 120 V residential electrical system. When a neutral wire breaks or opens, the utilization voltage can almost double to over 200 V with large leg-to-leg load imbalances. This extreme situation can result in almost four times the power and heat in loads. With such overheating, some loads can reach self-ignition temperatures in less than 10 minutes. Power Fault Circuit Interrupters (PFCIs) are designed to prevent fires from excess voltage across loads. Voltage-trip circuit breakers detect excess line voltages, but are unable to detect sub-circuit open neutral conditions.
Low line-voltage can cause electro-mechanical relays (on-off switches) to turn off (relay opens) and back on (relay closes again) in a repeating cycle. If there is current through the relay at that time, the opening process can create a parting arc across the relay contacts. The arc can melt, pit and oxidize the contact surfaces. This process can increase the resistance to current, superheat the relay and lead to fires. Power Fault Circuit Interrupters are designed to prevent fires from low voltage across loads.
* [http://www.inspect-ny.com/electric/AFCI-CPSC.htm AFCI Guide: Electrical Arc Fault Safety Advice for Homeowners & Home Inspectors] Friedman, Daniel J. [http://InspectAPedia.com InspectAPedia.com] Construction Inspection & Diagnosis Website
* [http://ulstandardsinfonet.ul.com/scopes/1699.html Underwriters Labs summary on UL 1699 standard on AFCIs]
* [http://www.AFCIsafety.org www.AFCIsafety.org - AFCI Educational Web site]
* [http://www.cpsc.gov/cpscpub/pubs/afcifac8.pdf CPSC AFCI Fact Sheet]
* [http://www.iaei.org/subscriber/magazine/00_e/mcmanus.htm AFCIs: Emerging Technology Solutions for Fires Resulting from Electrical Arcing] from "IAEI News: The Magazine"
* [http://www.zlan.com/ Zlan, Ltd.] is involved with research and development of AFCI technology.
* [http://www.ul.com/regulators/afci/categories.cfm] 6 types of AFCI's are listed by Underwriters Laboratory
Wikimedia Foundation. 2010.
Look at other dictionaries:
Circuit breaker — For other uses, see Circuit breaker (disambiguation). An air circuit breaker for low voltage (less than 1000 volts) power distribution switchgear … Wikipedia
Détecteur d'arc — Le détecteur d arc électrique est un appareil de protection électrique utilisable dans le domaine résidentiel. Cet appareil est installé dans le même tableau électrique comme les disjoncteurs. Sa fonction est de détecter les arcs électriques qui… … Wikipédia en Français
Prospective short circuit current — The prospective short circuit current (PSCC) is the highest electric current which can exist in a particular electrical system under short circuit conditions. It is determined by the voltage and impedance of the supply system. It is of the order… … Wikipedia
Residual-current device — A two pole residual current device A Residual Current Device is a generic term covering both RCCBs and RCBOs. A Residual Current Circuit Breaker (RCCB) is an electrical wiring device that disconnects a circuit whenever it detects that the… … Wikipedia
National Electrical Code — The National Electrical Code, 2008 edition The National Electrical Code (NEC), or NFPA 70, is a regionally adoptable standard for the safe installation of electrical wiring and equipment. The NEC, while having no legally binding regulation as… … Wikipedia
Electrical wiring (United States) — Electrical wiring in general refers to conductors used to carry electricity and their accessories. General aspects of electrical wiring as used to provide power in or to buildings and structures, commonly referred to as building wiring, are… … Wikipedia
Power line communication — or power line carrier (PLC), also known as power line digital subscriber line (PDSL), mains communication, power line telecom (PLT), power line networking (PLN), or broadband over power lines (BPL) are systems for carrying data on a conductor… … Wikipedia
NEMA connector — Twist lock connector redirects here. For the device used in intermodal shipping, see Twistlock. Ungrounded and grounded power plugs … Wikipedia
Electronic component — Various components An electronic component is a basic electronic element and may be available in a discrete form having two or more electrical terminals (or leads). These are intended to be connected together, usually by soldering to a printed… … Wikipedia
Electric shock — Electrocute redirects here. For the band, see Electrocute (band). An electric shock can occur upon contact of a human s body with any source of voltage high enough to cause sufficient current through the muscles or hair. The minimum current a… … Wikipedia