- CANDU reactor
The CANDU reactor is a Canadian-invented,
pressurized heavy water reactordeveloped initially in the late 1950s and 1960s by a partnership between Atomic Energy of Canada Limited(AECL), the Hydro-Electric Power Commission of Ontario(now known as Ontario Power Generation), Canadian General Electric(now known as GE Canada), as well as several private industry participants. The acronym "CANDU", a registered trademark of Atomic Energy of Canada Limited, stands for "CANada Deuterium Uranium". This is a reference to its deuterium-oxide ( heavy water) moderator and its use of uraniumfuel (originally, natural uranium). All current power reactors in Canadaare of the CANDU type. Canada markets this power reactor abroad.
The reactors are used in
nuclear power plantsto produce nuclear powerfrom nuclear fuel.
Schematic Diagram of a CANDU reactor: The primary loop is in yellow and orange, the secondary in blue and red. The cool heavy water in the calandria can be seen in pink, along with partially-inserted shutoff rods.
The CANDU reactor is conceptually similar to most
light water reactors, although it differs in the details.
Fission reactions in the
nuclear reactorcore heat a fluid, in this case heavy water(see below). This coolant is kept under high pressure to raise its boiling pointand avoid significant steamformation in the core. The hot heavy water generated in this "primary cooling loop" is passed into a heat exchangerheating light waterin the less-pressurized "secondary cooling loop". This water turns to steam and powers a conventional turbinewith a electrical generatorattached to it. Any excess heat energy in the steam after flowing through the turbine is rejected into the environment in a variety of ways, most typically into a large body of cool water, such as a lake, river or ocean. Heat can also be disposed of using a cooling tower, but they are avoided whenever possible because they reduce the plant's efficiency. More recently-built CANDU plants, such as the Darlington Nuclear Generating Stationnear Toronto, Ontario, use a discharge-diffuser system that limits the thermal effects in the environment to within natural variations.
At the time of its design, Canada lacked the heavy industry to cast and machine the large, heavy
steel pressure vesselused in most light water reactors. Instead, the pressure is contained in much smaller tubes, 10 cm diameter, that contain the fuel bundles. These smaller tubes are easier to fabricate than a large pressure vessel. In order to allow the neutrons to flow freely between the bundles, the tubes are made of zircaloy, which is highly transparent to neutrons. The zircaloy tubes are surrounded by a much larger low-pressure tank known as a calandria, which contains the majority of the moderator.
Canada also lacked access to
uranium enrichmentfacilities, which were then extremely expensive to construct and operate. The CANDU was therefore designed to use natural uranium as its fuel, like the ZEEPreactor, the first Canadian reactor. Traditional designs using light water as a moderator will absorb too many neutrons to allow a chain reactionto occur in natural uranium due to the low density of active nuclei. Heavy waterabsorbs fewer neutrons than light water, allowing a high neutron economy that can sustain a chain reaction even in unenriched fuel. Also, the low temperature of the moderator (below the boiling point of water) reduces changes in the neutrons' speeds from collisions with the moving particles of the moderator ("neutron scattering"). The neutrons therefore are easier to keep near the optimum speed to cause fissioning; they have good spectral purity. At the same time, they are still somewhat scattered, giving an efficient range of neutron energies.
thermal massof the moderator provides a significant heat sinkthat acts as an additional safety feature. If a fuel assembly were to overheat and deform within its fuel channel, the resulting change of geometry permits high heat transferto the cool moderator, thus preventing the breach of the fuel channel, and the possibility of a meltdown. Furthermore, because of the use of natural uranium as fuel, this reactor cannot sustain a chain reaction if its original fuel channel geometry is altered in any significant manner.
In a traditional light water reactor (LWR) design, the entire reactor core is a single large pressure vessel containing the light water, which acts as moderator and coolant, and the fuel arranged in a series of long bundles running the length of the core. To refuel such a reactor, it must be shut down, the pressure dropped, the lid removed, and a significant fraction of the core inventory, such as one-third, replaced in a batch procedure. The CANDU's calandria-based design allows individual fuel bundles to be removed without taking the reactor off-line, improving overall
duty cycleor capacity factor. A pair of remotely-controlled fueling machines visit each end of an individual fuel string. One machine inserts new fuel while the other receives discharged fuel.
A lower 235U density also generally implies that less of the fuel will be consumed before the fission rate drops too low to sustain criticality (due primarily to the relative depletion of 235U compared with the build-up of parasitic
fission products). However, by avoiding the uranium enrichment process, overall utilization of mined uranium in CANDU reactors is significantly less than in light-water reactors, about 30-40% less, using current designs.
A CANDU fuel assembly consists of a number of zircaloy tubes containing ceramic pellets of fuel arranged into a cylinder that fits within the fuel channel in the reactor. In older designs the assembly had 28 or 37 half-meter long fuel tubes with 12 such assemblies lying end to end in a fuel channel. The relatively new
CANFLEXbundle has 43 tubes, with two pellet sizes. It is about 10 cm (four inches) in diameter, 0.5 m (20 inches) long and weighs about 20 kg (44 lb) and replaces the 37-tube bundle. It has been designed specifically to increase fuel performance by utilizing two different pellet diameters.
A number of distributed light-water compartments called liquid zone controllers help control the rate of fission. The liquid zone controllers absorb excess neutrons and slow the fission reaction in their regions of the reactor core.
CANDU reactors employ two independent, fast-acting safety shutdown systems. Shutoff rods penetrate the calandria vertically and lower into the core in the case of a safety-system trip. A secondary shutdown system involves injecting high-pressure
gadolinium nitratesolution directly into the low-pressure moderator. [ cite web
url = http://www.nuclearfaq.ca/cnf_sectionA.htm#candu_control | title = Canadian Nuclear FAQ | work = The Canadian Nuclear FAQ by Dr. Jeremy Whitlock | accessdate= 2005-03-05 ]
Purpose of using heavy water
nuclear reactor physicsand nuclear fissionand heavy waterfor complete details." The key to maintaining a nuclear reactionwithin a nuclear reactoris to use the neutrons being released during fission to stimulate fission in other nuclei. With careful control over the geometry and reaction rates, this can lead to a self-sustaining chain reaction, a state known as "criticality". Natural uranium consists of a mixture of various isotopes, primarily 238U and a much smaller amount (about 0.72% by weight) of 235U. 238U can only be fissioned by neutrons that are fairly energetic, about 1 MeVor above. No amount of 238U can be made "critical", however, since it will tend to parasitically absorb more neutrons than it releases by the fission process. 235U, on the other hand, can support a self-sustained chain reaction, but due to the low natural abundance of 235U, natural uranium cannot achieve criticality by itself. The "trick" to making a working reactor is to slow some of the neutrons to the point where their probability of causing nuclear fission in 235U increases to a level that permits a sustained chain reaction in the uranium as a whole. This requires the use of a neutron moderator, which absorbs some of the neutrons' kinetic energy, slowing them down to an energy comparable to the thermal energy of the moderator nuclei themselves (leading to the terminology of " thermal neutrons" and "thermal reactors"). During this slowing-down process it is beneficial to physically separate the neutrons from the uranium, since 238U nuclei have an enormous parasitic affinity for neutrons in this intermediate energy range (a reaction known as "resonance" absorption). This is a fundamental reason for designing reactors with discrete solid fuel separated by moderator, rather than employing a more homogeneous mixture of the two materials. Water makes an excellent moderator. The hydrogenatoms in the water molecules are very close in mass to a single neutron and thus have a potential for high energy transfer, similar conceptually to the collision of two billiard balls. However, in addition to being a good moderator, water is also fairly effective at absorbing neutrons. Using water as a moderator will absorb enough neutrons that there will be too few left over to react with the small amount of 235U in natural uranium, again precluding criticality. So, light water reactors require fuel with an enhanced amount of 235U in the uranium, that is, enriched uraniumwhich generally contains between 3% and 5% 235U by weight (the waste from this process is known as depleted uranium, consisting primarily of 238U). In this enriched form there "is" enough 235U to react with the water-moderated neutrons to maintain criticality. One complication of this approach is the requirement to build uranium enrichmentfacilities which are generally expensive to build and operate. They also present a nuclear proliferationconcern since the same systems used to enrich the 235U can also be used to produce much more "pure" weapons-gradematerial (90% or more 235U), suitable for making a nuclear bomb. Operators could reduce these issues by purchasing ready-made fuel assemblies from the reactor supplier and have the latter reprocess the spent fuel. An alternative solution to the problem is to use a moderator that does "not" absorb neutrons as readily as water. In this case potentially all of the neutrons being released can be moderated and used in reactions with the 235U, in which case there "is" enough 235U in natural uranium to sustain criticality. One such moderator is heavy water, or deuterium-oxide. It reacts dynamically with the neutrons in a similar fashion to light water, albeit with less energy transfer on average given that heavy hydrogen, or deuterium, is about twice the mass of hydrogen. The advantage is that it already has the extra neutron that light water would normally tend to absorb, reducing the absorption rate. The use of heavy water moderator is the key to the CANDU system, enabling the use of natural uranium as fuel (in the form of ceramic UO2), which means that it can be operated without expensive uranium enrichment facilities. Additionally, the mechanical arrangement of the CANDU, which places most of the moderator at lower temperatures, is particularly efficient because the resulting thermal neutrons are "more thermal" than in traditional designs, where the moderator normally runs hot. This means that the CANDU is not only able to "burn" natural uranium and other fuels, but tends to do so more effectively as well.
Compared with light water reactors, a heavy water design is "neutron rich". This makes the CANDU design suitable for "burning" a number of alternative nuclear fuels. To date, the fuel to gain the most attention is
mixed oxide fuel(MOX). MOX is a mixture of natural uranium and plutonium, such as that extracted from former nuclear weapons. Currently, there is a worldwide surplus of plutonium due to the various agreements between the United States and the former Soviet Union to dismantle many of their warheads. However, the security of these supplies is a cause for concern. One way to address this security issue is by converting the warhead into fuel and burning the plutonium in a CANDU reactor.
Plutonium can also be extracted from spent nuclear fuel reprocessing. While this consists usually of a mixture of isotopes that is not attractive for use in weapons, it can be used in a MOX formulation reducing the net amount of nuclear waste that has to be disposed of.
Plutonium isn't the only fissile material in spent nuclear fuel that CANDU reactors can utilize. Because the CANDU reactor was designed to work with natural uranium, CANDU fuel can be manufactured from the used (depleted) uranium found in
light water reactor(LWR) spent fuel. Typically this "Recovered Uranium" (RU) has a U-235 enrichment of around 0.9%, which makes it unusable to an LWR, but a rich source of fuel to a CANDU (natural uranium has a U-235 abundance of roughly 0.7%). It is estimated that a CANDU reactor can extract a further 30-40% energy from LWR fuel by recycling it in a CANDU reactor.
Recycling of LWR fuel does not necessarily need to involve a reprocessing step. Fuel cycle tests have also included the DUPIC fuel cycle, or "direct use of spent PWR fuel in CANDU", where used fuel from a
pressurized water reactoris packaged into a CANDU fuel bundle with only physical reprocessing (cut into pieces) but no chemical reprocessing. Again, where light-water reactors require the reactivity associated with enriched fuel, the DUPIC fuel cycle is possible in a CANDU reactor due to the neutron economywhich allows for the low reactivity of natural uranium and used enriched fuel.
Several Inert-Matrix Fuels have been proposed for the CANDU design, which have the ability to "burn" plutonium and other
actinides from spent nuclear fuel, much more efficiently than in MOX fuel. This is due to the "inert" nature of the fuel, so-called because it lacks uranium and thus does not create plutonium at the same time as it is being consumed.
CANDU reactors can also breed fuel from natural
thorium, if uranium is unavailable.
The first CANDU-type reactor was
Nuclear Power Demonstration(NPD), in Rolphton, Ontario. It was intended as a proof-of-concept design, and was rated for only 22 MWe, a very low power for a commercial power reactor. It produced the first nuclear-generated electricity in Canada, and ran successfully from 1962 to 1987. [ cite web | author = Canadian Nuclear Society |url = http://www.cns-snc.ca/event/npd/npd_main_eng.htm | title = NPD Historical Plaque | date = 2007-07-07 ] [ [http://archives.cbc.ca/IDC-1-75-104-896/science_technology/candu/clip3] dead link|date=May 2008]
The second CANDU was the
Douglas Pointreactor, a more powerful version rated at roughly 200 MWeand located near Kincardine, Ontario. Douglas Point went into service in 1968, and ran until 1984. Uniquely among CANDU stations, Douglas Point incorporated an oil-filled window which offered a view of the east reactor face, even when the reactor was operating. The Douglas Point type was exported to India, and was the basis for India's fleet of domestically-designed and built 'CANDU-derivatives'. Douglas Point was originally planned to be a two-unit station, but the second unit was cancelled because of the success of the larger 515 MWe units at Pickering. [cite web | url = http://www.cns-snc.ca/history/DouglasPoint/DouglasPoint.html | author = Canadian Nuclear Society | title = The Douglas Point Story] [cite web | url = http://www.cns-snc.ca/history/DouglasPoint/AECL-2400/AECL2400-1.html | author = Canadian Nuclear Society | title = Douglas Point Nuclear Power Station]
In parallel to the development of the classic CANDU heavy-water design, experimental CANDU variants were developed.
WR-1, located at the AECL's Whiteshell Laboratoriesin Pinawa, Manitoba, used vertical pressure tubes and organic oil as the primary coolant. The oil used has a higher boiling point than water, allowing the reactor to operate at higher temperatures and lower pressures than a conventional reactor. This reactor operated successfully for many years, and promised a significantly higher thermal efficiency than water-cooled versions. Gentilly-1, near Trois-Rivières, Québec, was also an experimental version of CANDU, using a boiling light-water coolant and vertical pressure tubes, but was not considered successful and was closed after 7 years of fitful operation.
The successes at NPD and Douglas Point led to the decision to construct the first multi-unit station in Pickering, Ontario. Pickering A, consisting of units 1 to 4, went into service in 1971. Pickering B, consisting of units 5 to 8, went into service in 1983, giving a full-station capacity of 4,120 MWe. The station is placed very close to the city of
Toronto, in order to reduce transmission costs.
Pickering A was placed into voluntary lay-up in 1997, as a part of
Ontario Hydro's Nuclear Improvement plan. Units 1 and 4 have since been returned to service, although not without considerable controversy regarding significant cost-overruns, especially on Unit 4. (The refurbishment of Unit 1 was essentially on-time and on-budget, accounting for delays in project startup imposed by the Ontario provincial government.)
Ontario Power Generationannounced that refurbishment of Units 2 and 3 at Pickering A would not be pursued, contrary to expectations. The reason for this change in plan was economic: the material condition of these units was much poorer than had existed for Units 1 and 4, particularly the condition of the steam generators, and thus the refurbishment costs would be much higher. This rendered a return-to-service of Units 2 and 3 uneconomical. A project to decommission these units is currently in the early stages of planning.
The central functionality behind the CANDU design is heavy water moderation and on-line refuelling, which permits a range of fuel types to be used (including natural uranium, enriched uranium, thorium, and used fuel from Light Water Reactors). Significant fuel cost savings can be realized if the uranium does not have to be enriched, but simply formed into ceramic natural uranium-dioxide fuel. This saves not only on the construction of an enrichment plant, but also on the costs of processing the fuel.
However, some of this potential savings is offset by the initial, one time cost of the heavy water. The heavy water required must be more than 99.75% pure [cite web
url=http://www.nuclearfaq.ca/cnf_sectionA.htm#e|title=Canadian Nuclear FAQ
work=The Canadian Nuclear FAQ by Dr. Jeremy Whitlock|accessdate=March 5|accessyear=2005 [http://www.nuclearfaq.ca/cnf_sectionA.htm#e A. CANDU Nuclear Power Technology A.3 What is "heavy water"?] "reactor-grade" heavy water, nominally 99.75 wt% deuterium content."] and tonnes of this are required to fill the calandria and the heat transfer system. The next generation reactor (the
Advanced CANDU Reactor, also called the "ACR") mitigates this disadvantage by having a smaller moderator size and by using light water as a coolant.
Since heavy water is less efficient at transferring energy from neutrons, the moderator volume (relative to fuel volume) is larger in CANDU reactors compared with light-water designs, making a CANDU reactor core generally larger than a light water reactor of the same power output. In turn, this implies higher building costs for standard features like the
containment building. This is offset to some degree by the calandria-based construction, but even considering this, the CANDU tends to have higher capital costs compared with other designs. In fact, CANDU plant costs are dominated by construction costs, the price of fuel representing perhaps 10% of the cost of the power it delivers. This is true in general of nuclear plants, where the plant cost and cost of operations represent about 65% of overall lifetime cost. Due to the lower fuelling costs compared to light water reactor designs, the levelized lifetime cost on a "per-kWh" basis tends to be comparable to these other designs.
When first being offered, CANDUs offered much better "running" time statistics, the
capacity factor, than light-water reactors of a similar generation. At the time, light-water (LWR) designs spent, on average, about half of their time in maintenance or refueling outages. However, since the 1980s dramatic improvements in LWR outage management have narrowed the gap between LWR and CANDU, with several LWR units achieving capacity factors in the 90% and higher range, with an overall fleet performance of 89.5% in 2005. [ [http://www.nei.org/documents/U.S.%20Nuclear%20Industry%20is%20Achieving%20Record%20Levels%20of%20Performance.pdf US Fleet Performance] ] The latest-generation CANDU 6 reactors have demonstrated an 88-90% capacity factor, but overall fleet performance is dominated by the older Canadian units which generally report capacity factors on the order of 80%. [ [http://www.cns-snc.ca/branches/Toronto/energy/wind_vs_nuclear.doc CANDU Lifetime Performance to November 30, 2001] ]
Some CANDU plants suffered from cost overruns during construction, primarily due to external factors. For instance, a number of imposed construction delays led to roughly a doubling of the projected cost of the Darlington Nuclear Generating Station near Toronto, Ontario. Technical problems and redesigns added about another billion to the resulting $14.4 billion price. [ [http://www.canducanada.ca/eng/darlington.html Team CANDU, Debunking Darlington] ] [ [http://www.magma.ca/~jalrober/CANcosts.htm "Can CANDU estimates be trusted?"] by J.A.L. Robertson (2004)] In contrast, the two CANDU 6 reactors more recently installed in China at the Qinshan site were completed on-schedule and on-budget, an achievement attributed to tight control over scope and schedule. [ The company SNC-Lavalin has had the best record in constructing a power plant of this size. [http://www.canducanada.ca/eng/budget.html Team CANDU, "On Budget, On Time"] ]
=Nuclear nonproliferation= In terms of safeguards against
nuclear proliferation, CANDU reactors meet a similar level of international certification as other reactor designs. However, there is a common misconception that the plutonium for India's first nuclear detonation, conducted in 1974 Operation Smiling Buddha, was produced in a CANDU design. In fact, the plutonium was produced in the unsafeguarded CIRUSreactor that is based on the NRXdesign, a Canadian research reactor design. In addition to its two CANDU reactors, India has some unsafeguarded pressurised heavy water reactors (PHWRs) based on the CANDU design, and two safeguarded light-water reactors supplied by the US. Plutonium has been extracted from the spent fuel from all of these sources in the PREFREreprocessing facility. [cite journal | url = http://www.wisconsinproject.org/pubs/articles/1987/stoppingindianbomb.htm
first = Gary
last = Milhollin
journal = The American Journal of International Law
year = 1987
month = July
title = Stopping the Indian Bomb
doi = 10.2307/2202014
volume = 81
pages = 593] While all of these reactors could in principle be used for plutonium production, India uses an Indian designed and built military reactor for plutonium production called
Dhruva. It is believed that the Dhruva reactor design is derived from the CIRUS reactor, with the Dhruva being scaled-up for more efficient plutonium production. It is this reactor which is thought to have produced the plutonium for India's more recent (1998) Operation Shaktinuclear tests. [cite journal
first = David
last = Albright
coauthors = and Mark Hibbs
year = 1992
month = September
title = India's Silent Bomb
journal = Bulletin of the Atomic Scientist
volume = 48
issue = 7
pages = pp. 27–31
url = http://www.thebulletin.org/article.php?art_ofn=sep92albright
format = dead link|date=June 2008 – [http://scholar.google.co.uk/scholar?hl=en&lr=&q=author%3AAlbright+intitle%3AIndia%27s+Silent+Bomb&as_publication=Bulletin+of+the+Atomic+Scientist&as_ylo=1992&as_yhi=1992&btnG=Search Scholar search] ]
Another concern is
tritiumproduction. Although heavy water is relatively immune to neutron capture, a small amount of the deuterium turns into tritium via this process. Tritium, when mixed with deuterium, undergoes nuclear fusionmore easily than any other elemental mixture. Small amounts of tritium can be used in both the "trigger" of an A-bomband the "fusion boost" of a boosted fission weapon. Tritium can also be used in the main fusion process of an H-bomb, but in this application it is typically generated "in situ" by neutron irradiation of lithium-6.
Tritium is extracted from some CANDU plants in operation in Canada, primarily to improve safety in case of heavy-water leakage. The gas is stockpiled and used in a variety of commercial products, notably "powerless" lighting systems and medical devices. In 1985 what was then Ontario Hydro sparked controversy in Ontario due to its plans to sell tritium to the US. The plan, by law, involved sales to non-military applications only, but some speculated that even this minor penetration of the market would aid the U.S. nuclear weapon program. Demands for this supply in the future appear to outstrip production; in particular the needs of future generations of experimental
fusion reactors like ITERwill use up a significant amount of any potential stockpile. Currently between 1.5 and 2.1 kg of tritium are recovered yearly at the Darlington separation facility, of which a minor fraction is sold. [ [http://public.lanl.gov/willms/Presentations/Tritium_Supply_Considerations.pdf] dead link|date=May 2008 ]
Operation Shaktitest series in India included one bomb of about 45 kT yield that India has publicly claimed was a hydrogen bomb. An offhand comment in the BARCpublication "Heavy Water - Properties, Production and Analysis" appears to suggest that the tritium was extracted from the heavy water in the CANDU and PHWR reactors in commercial operation. "Janes Intelligence Review" quotes the Chairman of the Indian Atomic Energy Commission as admitting to the tritium extraction plant, but refusing to comment on its use. [cite web | url = http://www.ccnr.org/india_tritium.html | author = Canadian Coalition for Nuclear Responsibility | title = Tritium from Power Plants gives India an H-bomb capability | date = 1996-03-27] It is known, however, that India has developed the technology to create tritium from the neutron-irradiation of lithium-6 in reactors, a process that is several orders of magnitude more efficient than the extraction of tritium from irradiated heavy water.
Active CANDU reactors
Today there are 29 CANDU reactors in use around the world, and a further 13 "CANDU-derivatives" in use in India (these reactors were developed from the CANDU design after India detonated a nuclear bomb in 1974 and Canada stopped nuclear dealings with India).The countries the reactors are located in are:
Canada: 17 (+3 refurbishing, +5 decommissioned)
South Korea: 4
India: 2 (+13 CANDU-derivatives in use, +3 CANDU-derivatives under construction)
Romania: 2 (+3 under construction, currently dormant)
Interest continues to be expressed in new CANDU construction around the world, and CANDU technology is typically involved in open bidding processes alongside LWR technology.
CANDU reactors have been proposed as the main vehicle for planned supply replacement and growth in
Ontario, Canada, a province that currently generates over 50% of its electricity from CANDU reactors, with Canadian government help with financing. [cite news|url=http://www.reuters.com/article/marketsNews/idUSN0743618220080807?sp=true|title=Canada nuclear firms seek Ottawa financing|date=Aug 7, 2008|publisher= Reuters|accessdate=2008-08-10] Interest has also been expressed in Western Canada, where CANDU reactors are being considered as heat and electricity sources for the energy-intensive oil sands extraction process, which currently uses natural gas. Energy Alberta Corporation, headquartered in Calgary, announced August 27 2007that they had filed application for a license to build a new nuclear plant at Lac Cardinal (30 km west of the town of Peace River, Alberta). The application would see an initial twin AECLACR-1000 plant go online in 2017, producing 2.2 gigawatt(electric). [ [http://www.albertaindex.com/content/view/213/1/ Lac Cardinal (Alberta Index)] ] [ [http://www.cbc.ca/money/story/2007/08/28/alberta-nuclear.html Lac Cardinal (CBC) 2007-08-28] ] [ [http://www.thehilltimes.ca/pdf/2007/060407_ht.pdf "The Hill Times" page 26, 2007-06-04] ] Romaniais in discussions for the completion of its multi-unit nuclear plant at Cernavoda, now consisting of two operating CANDU reactors. Three more partially-completed CANDU reactors exist on the same site, part of a project discontinued at the close of the Nicolae Ceauşescuregime. Turkeyhas repeatedly shown interest in the CANDU reactor, but so far has chosen not to pursue nuclear energy. In the summer of 2006, Turks protested against plans for building nuclear reactors.
Enhanced CANDU 6
The Enhanced CANDU 6 is an evolutionary upgrade of the standard CANDU 6 design rated to deliver a gross output of 740 MWe per unit.
The units are designed with a planned operating life of over fifty years, which will be achieved with a mid-life program to replace some of the key components, such as the fuel channels. The plants have a projected average annual capacity factor of more than nintety per cent.
Enhancement of the CANDU 6 design to achieve higher plant output include: the installation of an Ultrasonic Flow Meter (UFM) to improve the accuracy of feedwater flow measurements, improvements in turbine design itself and change in condenser vacuum system design for operation at lower condenser pressures.
AECL continues to develop other features to further improve the plant’s performance while maintaining the basic features of the CANDU 6 design, which over time have proven to be extremely reliable with an excellent production record since the early 1980s. The additional enhancements include:
*Increased plant margins, both operational and safety
*Enhanced environmental protection
*Improved Severe Accident Response
*Improved Fire Protection System
*Improved Plant Security
*Modern Computers and Control Systems
*Improved Plant Operability and Maintainability
*Optimized Plant Maintenance Outages
*Reduced Overall Project Schedule
*Advanced MACSTOR Design for Spent Fuel Storage
Advanced CANDU Reactor (ACR-1000)
The ACR-1000 represents the continuing evolution of CANDU design to match changing market conditions. ACR-1000 is the next-generation (officially, "Generation III+") CANDU technology from Atomic Energy of Canada Ltd. (AECL), which maintains proven elements of existing CANDU design, while making some significant modifications:
*compact fuel-channel design, generating over 50% more power than a conventional CANDU-6 reactor, with approximately the same overall core diameter;
*improved thermal efficiency through higher-pressure steam turbines (13 MPa primary pressure; 7 MPa steam outlet pressure, vs. approximately 10 MPa and 5 MPa, respectively, in current designs);
*pressurized light-water coolant;
*negative coolant void reactivity;
*reduction in used fuel production by over 30%;
*greater thermal efficiency due to higher operating temperatures and pressures;
*reduced use of heavy water (more than half, for the same power output), thus reducing cost and eliminating many material handling concerns;
*use of slightly enriched uranium (about 2%) to extend fuel life to three times that of existing *natural uranium fuel (reducing fuel waste volume by two-thirds);
*average channel power increased from roughly 6 MW (CANDU 6) to roughly 7 MW;
*flatter neutron flux shape, allowing 14% lower peak fuel element ratings;
*longer plant operational lifetime (60 years);
*longer operating cycles between maintenance outages (3 years);
*90% design capacity factor;
*pre-stressed concrete containment (1.8 m thick) with steel liner; and
*further additions to CANDU's inherent passive safety.
At the same time the basic and defining design features of CANDU are all maintained:
*modular, horizontal fuel channel core;
*heavy water moderation;
*simple, economical fuel bundle;
*separate, cool, low-pressure moderator with back-up heat sink capability;
*two independent, fast-acting shutdown systems;
*ability to perform long-term flux-shaping and failed fuel management through on-line refuelling.
It is expected that the capital cost of constructing these plants will be reduced by up to 40% compared to current CANDU 6 plants.
Tritiumis a radioactive form of hydrogen(H-3), with a half-lifeof 12.3 years. It is found in small amounts in nature (about 4 kg globally), created by cosmic rayinteractions in the upper atmosphere. Tritium is considered to be a weak radionuclidebecause of the low energy of its radioactive emissions ( beta particleenergy 0 -19 keV) [http://www.nuclearfaq.ca/ReviewofGreenpeacereport_Final.pdf reviewed by Dr. Richard Osborne] . The beta particles do not travel very far in air and no do not penetrate skin; therefore the main biological hazard of tritium is due to its intake into the body (inhalation, ingestion, or absorption).
Tritium is generated in all nuclear power designs; however, CANDU reactors generate more tritium in their coolant and moderator than light-water designs, due to
neutron capturein heavy hydrogen. Some of this tritium escapes into containment and is generally recovered; however a small percentage (about 1%) escapes containment and constitutes a routine radioactive emission from CANDU plants (also higher than from an LWR of comparable size). Operation of a CANDU plant therefore includes monitoring of this effluent in the surrounding biota (and publishing the results), in order to ensure that emissions are maintained below regulatory limits.
In some CANDU reactors the tritium concentration in the moderator is periodically reduced by an extraction process, in order to further reduce this risk. Typical tritium emissions from CANDU plants in Canada are less than 1% of the national regulatory limit, which is based upon the guidelines of the
International Commission on Radiological Protection(ICRP) [http://www.opg.com/safety/nsafe/nuclear/faq.asp] (for example, the maximum permitted drinking water concentration for tritium in Canada [http://www.hc-sc.gc.ca/ewh-semt/water-eau/drink-potab/guide/index-eng.php] , 7000 Bq/L, corresponds to 1/10 of the ICRP's public dose limit). Tritium emissions from other CANDU plants are similarly low [http://www.djs.si/proc/port2001/pdf/508.pdf] [http://www.nirs.org/radiation/tritium/tritium06122007gphazardreport.pdf] .
In general there is significant public controversy associated with radioactive emissions from nuclear power plants, and for CANDU plants one of the main concerns is tritium. In 2007
Greenpeacepublished a [http://www.greenpeace.org/raw/content/canada/en/documents-and-links/publications/tritium-hazard-report-pollu.pdf critique of tritium emissions] from Canadian nuclear power plants by Dr. Ian Fairlie. This report was [http://www.nuclearfaq.ca/ReviewofGreenpeacereport_Final.pdf reviewed by Dr. Richard Osborne] and found to be in significant error.
Nuclear power in Canada
List of nuclear reactors
Embalse nuclear power plant
* [http://www.nuclearfaq.ca/brat_fuel.htm The Evolution of CANDU Fuel Cycles and Their Potential Contribution to World Peace]
* [http://www.candu.org/ CANDU Owner's Group]
* [http://www.candu.org/candu_reactors.html A history of the CANDU reactor]
* [http://canteach.candu.org/ CANTEACH - Educational and Reference Library on Candu Technology]
* [http://www.opg.com/default2.asp Ontario Power Generation]
* [http://www.brucepower.com/ Bruce Power]
* [http://www.nbpower.com/en/ New Brunswick Power]
* [http://www.hydroquebec.com/ Hydro-Québec]
* [http://www.aecl.ca/ Atomic Energy of Canada Limited]
* [http://www.nuclearsafety.gc.ca/ Canadian Nuclear Safety Commission]
* [http://www.cns-snc.ca/ Canadian Nuclear Society]
* [http://www.cna.ca/ Canadian Nuclear Association]
* [http://www.nuclearfaq.ca Canadian Nuclear FAQ]
* [http://archives.cbc.ca/IDD-1-75-104/science_technology/candu/ CBC Digital Archives - Candu: The Canadian Nuclear Reactor]
* [http://canteach.candu.org/library/19910101.pdf Chernobyl – A Canadian Perspective]
* [http://www.walrusmagazine.com/articles/2006.09-energy-candu-reactor/ Will CANDU do? Walrus Magazine]
Wikimedia Foundation. 2010.
Look at other dictionaries:
Advanced CANDU Reactor — The Advanced CANDU Reactor (ACR) is a Generation III+ design and is a further development of existing CANDU reactors designed by Atomic Energy of Canada Limited. It is a light water cooled reactor that incorporates features of both Pressurised… … Wikipedia
Advanced CANDU Reactor — Der Advanced CANDU Reactor (kurz ACR) ist eine Weiterentwicklung der CANDU Reaktoren von Atomic Energy of Canada Limited. Dieser ist ein leichtwassergekühlter Reaktor. Wie bei allen CANDU Reaktoren wird als Moderator schweres… … Deutsch Wikipedia
CANDU Owner's Group — The CANDU Owners Group Inc. (COG) is a not for profit organization with voluntary funding from CANDU owning utilities and AECL.It is dedicated to providing programs for cooperation, mutual assistance and exchange of information for the successful … Wikipedia
CANDU-Reaktor — Schema eines CANDU Reaktors 1 Brennelement 8 Brennelement Wechselmaschine 2 Moderatortank (Calandria) (drucklos) 9 … Deutsch Wikipedia
CANDU — Schema eines CANDU Reaktors Brennstoffbündel eines CANDU Reaktors Ein CANDU Reaktor (CANada Deuterium Uranium) ist ein Schwerwasserreaktor, der von der … Deutsch Wikipedia
Candu-Reaktor — Schema eines CANDU Reaktors Brennstoffbündel eines CANDU Reaktors Ein CANDU Reaktor (CANada Deuterium Uranium) ist ein Schwerwasserreaktor, der von der … Deutsch Wikipedia
Reactor vessel — In a nuclear power plant, the reactor vessel is a pressure vessel containing the coolant and reactor core. Not all power reactors have a reactor vessel. Power reactors are generally classified by the type of coolant rather than the by the… … Wikipedia
Reactor CANDU — Saltar a navegación, búsqueda El reactor CANDU es un reactor de agua pesada presurizada (PHWR sus siglas en inglés) diseñado a finales de los años 1950 y en los años 1960 por una asociación entre Atomic Energy of Canada Limited (AECL) y la Hydro… … Wikipedia Español
Reactor ZED-2 — Saltar a navegación, búsqueda El reactor ZED 2 (Zero Energy Deuterium) es el sucesor del reactor ZEEP. Diseñado por AECL para soporte del reactor CANDU, la unidad alcanzó su primera criticidad en septiembre de 1960. El reactor está todavía en… … Wikipedia Español
Reactor ZEEP — Saltar a navegación, búsqueda El reactor ZEEP (Zero Energy Experimental Pile) era un reactor nuclear que se construyó en los Chalk River Laboratories cerca del río Chalk, en Ontario, Canadá. ZEEP alcanzó por primera vez su criticidad a las 3:45… … Wikipedia Español