- Heat pump
A heat pump is a machine or device that moves
heatfrom one location (the 'source') to another location (the 'sink' or 'heat sink'), using work. Most heat pump technology moves heat from a low temperature 'heat source" to a higher temperature "heat sink". [The Systems and Equipment volume of the " ASHRAE Handbook", ASHRAE, Inc., Atlanta, GA, 2004] Common examples are food refrigerators and freezers, air conditioners, and reversible-cycle "heat pumps" for providing thermal comfort. Heat pumps can also operate in reverse, producing heat. This produces an effcient way of drying, and manufacturers such as AEG and Miele have released tumble dryers that utilise this method. It is claimed to be more energy saving and quicker than conventional drying.
Heat pumps can be thought of as a
heat enginewhich is operating in reverse. One common type of heat pump works by exploiting the physical properties of an evaporating and condensing fluid known as a refrigerant. In heating, ventilation, and cooling ( HVAC) applications, a heat pump normally refers to a vapor-compression refrigerationdevice that includes a reversing valve and optimized heat exchangersso that the direction of heat flow may be reversed. Most commonly, heat pumps draw heat from the air or from the ground. Air-source heat pumps with a coefficient of performance(COP) 3 are developed in Japan at −20 °C.
According to the
second law of thermodynamicsheat cannot spontaneously flow from a colder location to a hotter area; work is required to achieve this. ["Fundamentals of Engineering Thermodynamics", by Howell and Buckius, McGraw-Hill, New York, 1987] Heat pumps differ in how they apply this work to move heat, but they can essentially be thought of as heat engines operating in reverse. A heat engine allows energy to flow from a hot 'source' to a cold heat 'sink', extracting a fraction of it as work in the process. Conversely, a heat pump requires work to move thermal energy from a cold source to a warmer heat sink.
Since the heat pump uses a certain amount of work to move the heat, the amount of energy deposited at the hot side is greater than the energy taken from the cold side by an amount equal to the work required. Conversely, for a heat engine, the amount of energy taken from the hot side is greater than the amount of energy deposited in the cold heat sink since some of the heat has been converted to work.
One common type of heat pump works by exploiting the physical properties of an evaporating and condensing fluid known as a
refrigerant. . This device then passes the low pressure, (almost) liquid refrigerant to another heat exchanger, the evaporator where the refrigerant evaporates into a gas via heat absorption. The refrigerant then returns to the compressor and the cycle is repeated.
In such a system it is essential that the refrigerant reaches a sufficiently high temperature when compressed, since the second law of thermodynamics prevents heat from flowing from a cold fluid to a hot heat sink. Similarly, the fluid must reach a sufficiently low temperature when allowed to expand, or heat cannot flow from the cold region into the fluid. In particular, the pressure difference must be great enough for the fluid to condense at the hot side and still evaporate in the lower pressure region at the cold side. The greater the temperature difference, the greater the required pressure difference, and consequently more energy is needed to compress the fluid. Thus as with all heat pumps, the energy efficiency (amount of heat moved per unit of input work required) decreases with increasing temperature difference.
Due to the variations required in temperatures and pressures, many different refrigerants are available. Refrigerators, air conditioners, and some heating systems are common applications that use this technology.
HVACapplications, a heat pump normally refers to a vapor-compression refrigerationdevice that includes a reversing valve and optimized heat exchangersso that the direction of heat flow may be reversed. The reversing valve switches the direction of refrigerant through the cycle and therefore the heat pump may deliver either heating or cooling to a building. In the cooler climates the default setting of the reversing valve is heating. The default setting in warmer climates is cooling. Because the two heat exchangers, the condenser and evaporator, must swap functions, they are optimized to perform adequately in both modes. As such, the efficiency of a reversible heat pump is typically slightly less than two separately-optimized machines.
plumbingapplications, a heat pump is sometimes used to heat or preheat water for swimming pools or domestic water heaters.
In somewhat rare applications, both the heat extraction and addition capabilities of a single heat pump can be useful, and typically results in very effective use of the input energy. For example, when an air cooling need can be matched to a water heating load, a single heat pump can serve two useful purposes. Unfortunately, these situations are rare because the demand profiles for heating and cooling are often significantly different.
Until the 1990s, the
refrigerants were often chlorofluorocarbons such as R-12 ( dichlorodifluoromethane), one in a class of several refrigerants using the brand name Freon, a trademark of DuPont. Its manufacture was discontinued in 1995 because of the damage that CFCscause to the ozone layerif released into the atmosphere. One widely-adopted replacement refrigerant is the hydrofluorocarbon (HFC) known as R-134a(1,1,1,2-tetrafluoroethane). R-134a is not as efficient as the R-12 it replaced (in automotive applications) and therefore, more energy is required to operate systems utilizing R-134a than those using R-12. Other substances such as liquid ammonia, or occasionally the less corrosive but flammable propaneor butane, can also be used.
carbon dioxide, R-744, has increasingly been used, utilizing the transcritical cycle. In residential and commercial applications, the hydrochlorofluorocarbon (HCFC) R-22 is still widely used, however, HFC R-410adoes not deplete the ozone layer, but it is a powerful global warming gas and is nevertheless increasingly being used. Hydrogen, helium, nitrogen, or plain air is used in the Stirling cycle, providing the maximum number of options in environmentally friendly gases.More newer refrigerators are now exploiting the R600A which is isobutane, and does not deplete the ozone and is friendly to the environment.
When comparing the performance of heat pumps, it is best to avoid the word "efficiency" which has a very specific thermodynamic definition. The term
coefficient of performance(COP) is used to describe the ratio of useful heat movement to work input. Most vapor-compression heat pumps utilize electrically powered motors for their work input. However, in most vehicle applications shaft work, via their internal combustion engines, provide the needed work.
When used for heating a building on a mild day, a typical
air-source heat pumphas a COP of 3 - 4, whereas a typical electric resistance heaterhas a COP of 1.0. That is, one jouleof electrical energy will cause a resistance heater to produce one joule of useful heat, while under ideal conditions, one joule of electrical energy can cause a heat pump to move much more than one joule of heat from a cooler place to a warmer place. Sometimes this is inappropriately expressed as an efficiency value greater than 100%, as in the statement, "XYZ brand heat pumps operate at up to 400% efficiency!" This is inaccurate, since the work does not "make" heat, but instead "moves" existing heat "upstream"; otherwise, this would be a perpetual-motion machine. The effective heating per wattof electric energy used can be up to 450% as much as resistance heating however, making this more an issue of semantics than science.
Note that when there is a wide temperature differential, e.g., when an air-source heat pump is used to heat a house on a very cold winter day, it takes more work to move the same amount of heat indoors than on a mild day. Ultimately, due to Carnot efficiency limits, the heat pump's performance will approach 1.0 as the outdoor-to-indoor temperature difference increases. This typically occurs around −18 °C (0 °F) outdoor temperature for air source heat pumps. Also, as the heat pump takes heat out of the air, some moisture in the outdoor air may condense and possibly freeze on the outdoor heat exchanger. The system must periodically melt this ice. In other words, when it is extremely cold outside, it is simpler, and wears the machine less, to heat using an electric-resistance heater than to strain an air-source heat pump. (
Geothermal heat pumps are dependent upon the temperature underground, which is "mild" all year round. Their COP is therefore always in the range of 3.5-4.0).
In cooling mode a heat pump's operating performance is described as its
energy efficiency ratio(EER) or seasonal energy efficiency ratio(SEER), and both measures have units of BTU/(h·W). A larger EER number indicates better performance. The manufacturer's literature should provide both a COP to describe performance in heating mode and an EER or SEER to describe performance in cooling mode. Actual performance varies, however, and depends on many factors such as installation, temperature differences, site elevation, and maintenance.
Heat pumps are more "effective" for heating than for cooling if the temperature difference is held equal. This is because the compressor's input energy is largely converted to useful heat when in heating mode, and is discharged along with the moved heat via the condenser. But for cooling, the condenser is normally outdoors, and the compressor's dissipated work is rejected rather than put to a useful purpose.
For the same reason, opening a food refrigerator or freezer heats up the kitchen rather than cooling it because its refrigeration cycle rejects heat to the indoor air. This heat includes the compressor's dissipated work as well as the heat removed from the inside of the appliance.
The COP for a heat pump in a heating or cooling application, with steady-state operation, is:
* is the amount of heat extracted from a cold reservoir at temperature ,
* is the amount of heat delivered to a hot reservoir at temperature ,
* is the compressor's dissipated work.
CoP and Lift
The CoP increases as the temperature difference, or "Lift", decreases between heat source and destination. The CoP can be maximised at design time by choosing a heating system requiring only a low final water temperature (e.g. underfloor heating), and by chosing a heat source with a high average temperature (e.g. the ground). Domestic Hot Water (DHW) and radiators require high water temperatures, affecting the choice of heat pump technology.
Most commonly, heat pumps draw heat from the air (outside or inside air) or from the ground (
groundwateror soil) [ [http://www2.vlaanderen.be/economie/energiesparen/doc/folder_warmtepomp.pdf Heat pumps sources including groundwater, soil, outside and inside air)] ] . The heat drawn from the ground is in most cases stored solar heat, and it should not be confused with geothermalheat, though the latter will contribute in some small measure to all heat in the ground. Other heat sources include water; nearby streams and other natural water bodies have been used, and sometimes domestic waste water which is often warmer than the ambient temperature.
Types of heat pumps
A number of sources have been used for the heat source for heating private and communal buildings [ [http://www1.eere.energy.gov/geothermal/pdfs/26161b.pdf Homeowners using heat pump systems] ] . The two main types of heat pumps are
compressionheat pumps and absorptionheat pumps. Compression heat pumps always operate on mechanical energy (through electricity), while absorption heat pumps may also run on heat as an energy source (through electricity or burnable fuels). [ [http://www2.vlaanderen.be/economie/energiesparen/doc/brochure_warmtepomp.pdf Types of heat pumps (see page 8)] ]
Air-source heat pumps
Air source heat pumpsare relatively easy (and inexpensive) to install and have therefore historically been the most widely used heat pump type. However, they suffer limitations due to their use of the outside air as a heat source or sink. The higher temperature differential during periods of extreme cold or heat leads to a lower efficiency, as explained above. In mild weather, COP may be around 3.5, while at temperatures below around −5°C (23°F) an air-source heat pump's COP will drop below 2. But Air-source heat pumps with a COP 3 are developed in Japan at −20 °C. The average COP over seasonal variation is typically 2.5-2.8,high efficiency model in Japan over 6.0(2.8kW). [ [http://www.residential.carrier.com/products/acheatpumps/heatpumps/index.shtml Carrier web site: Heat Pumps] ] [ [http://www.hptcj.or.jp/about_e/contribution/pdf/hpe-all.pdf Heat Pumps Long Awaited Way out of the Global Warming] ] Domestic air-source heatpump water heater called Eco-cute was developed in 2001.
Geothermal heat pumps
Geothermal heat pumps typically have higher efficiencies than air-source heat pumps. This is because they draw heat from the ground or groundwaterwhich is at a relatively constant temperature all year round below a depth of about eight feet (2.5 m). This means that the temperature differential is lower, leading to higher efficiency. Ground-source heat pumps typically have COPs of 3.5-4.0 with little seasonal variation. The tradeoff for this improved performance is that a ground-source heat pump is more expensive to install due to the need for the digging of wells or trenches in which to place the pipes that carry the heat exchange fluid. When compared versus each other, groundwater heat pumps are generally more efficient than heat pumps using heat from the soil.
olid state heat pumps
In 1881, the German physicist
Emil Warburgput a block of iron into a strong magnetic field and found that it increased very slightly in temperature. Some commercial ventures to implement this technology are underway, claiming to cut energy consumption by 40% compared to current domestic refrigerators . [Guardian Unlimited, December 2006 [http://environment.guardian.co.uk/energy/story/0,,1971818,00.html 'A cool new idea from British scientists: the magnetic fridge'] ] The process works as follows: Powdered gadoliniumis moved into a magnetic field, heating the material by 2 to 5 °C. The heat is removed by a circulating fluid. The material is then moved out of the magnetic field, reducing its temperature below its starting temperature.
After the heat has been absorbed from the source (air or ground), the heat is transferred and used in the home or building (for
space heating. This is generally done by pipes in the floor, wallor ceiling[ [http://www2.vlaanderen.be/economie/energiesparen/doc/brochure_warmtepomp.pdf Heat pumps used with floor, ceiling and wall heating for space heating] ] . The heat pump can also be used to heat water (thus in solar hot water systems), yet this is generally not done as it is much less efficient. Finally, the heat pumps may also be used to cool the house (eg in summer) [ [http://oee.nrcan.gc.ca/publications/infosource/pub/home/Heating_and_Cooling_with_a_Heat_Pump_Section4.cfm Explanation of heating and cooling with heat pumps by NRCAN] ] . However, the latter is also less efficient, and therefore less commonly practiced. [ [http://www2.vlaanderen.be/economie/energiesparen/doc/brochure_warmtepomp.pdf Other uses with heat pumps] ]
* 1834 –
Jacob Perkinsbuilt refrigeratorwith diethyl ether;
* 1852 – Lord Kelvin built first heat pump.
Geothermal heat pump
Geothermal exchange heat pump
Thermoelectricheat pumps that use the Peltier effect
* [http://www.hptcj.or.jp/about_e/contribution/pdf/hpe-all.pdf Heat Pumps Long Awaited Way out of the Global Warming] - Information from Heat Pump & Thermal Storage Technology Center of Japan
* [http://www1.eere.energy.gov/geothermal/heatpumps.html Practical information on setting up heat pump systems at home]
* [http://geoexchange.us/illustrations/graphics.htm Pictures on private/communal heat pump installations]
* [http://www.heatpumpcentre.org/ International Energy Agency Heat Pump Programme, Information site for heat pumping technology]
* (Dutch) [http://www.energiesparen.be/algemeen/klik.php?link=http://www2.vlaanderen.be/ned/sites/economie Useful publication called ""Warmtepompen voor woningverwarming"] . Info on heat pump systems with drawings, schematics and explications of practically set-up systems).
* (Dutch) [http://www2.vlaanderen.be/economie/energiesparen/doc/folder_warmtepomp.pdf Useful publication called "Warmtepompen - De natuur als bron van verwarming"] . Info on heat pump systems with drawings, schematics and explications.
* [http://knowledge.allianz.com/en/globalissues/climate_change/climate_solutions/heat_pump_street.html Road Energy Systems: Heat from the Street] Article on heat pump systems installed in roads and parking lots. Allianz Knowledge, June 2008
* [http://oee.nrcan.gc.ca/publications/infosource/home/index.cfm?act=online&id=4427&format=PDF&lang=01&PrintView=N&Text=N Heating and Cooling with a Heat pump] - Information from the Canadian Government's Natural Resources Department, Office of Energy Efficiency
Wikimedia Foundation. 2010.
Look at other dictionaries:
heat pump — n. a device for cooling or warming an enclosed space by removing heat from interior air and transferring it out, or by absorbing heat from outdoor air, or from a hot water source, and transferring it in … English World dictionary
heat pump — n part of a machine that takes heat from one place to another … Dictionary of contemporary English
heat pump — heat′ pump n. ene thr a device that uses a compressible refrigerant to transfer heat in a reversible process from one body, as the ground, air, or water, to another body, as a building • Etymology: 1890–95 … From formal English to slang
Heat pump — 1) (air source) An air source heat pump is the most common type of heat pump. The heat pump absorbs heat from the outside air and transfers the heat to the space to be heated in the heating mode. In the cooling mode the heat pump absorbs heat … Energy terms
heat pump — noun apparatus that extracts heat from a liquid that is at a higher temperature than its surroundings; can be used to transfer heat from a reservoir outside in order to heat a building • Hypernyms: ↑apparatus, ↑setup * * * noun : a device for… … Useful english dictionary
heat pump — a device that uses a compressible refrigerant to transfer heat from one body, as the ground, air, or water, to another body, as a building, with the process being reversible. [1890 95] * * * Device for transferring heat from a substance or space… … Universalium
heat pump — UK / US noun [countable] Word forms heat pump : singular heat pump plural heat pumps a piece of equipment that carries heat from one place to another, for example in a fridge … English dictionary
heat pump — šiluminis siurblys statusas T sritis automatika atitikmenys: angl. heat pump vok. Wärmepumpe, f rus. тепловой насос, m pranc. pompe à chaleur, f … Automatikos terminų žodynas
heat pump — /ˈhit pʌmp/ (say heet pump) noun an apparatus, usually electrical, which both heats and cools a building, as required, by transferring heat either from or to a larger reservoir of heat such as a body of groundwater, the air, etc … Australian English dictionary
Heat Pump — An electricity powered device that extracts available heat from one area (the heat source) and transfers it to another (the heat sink) to either heat or cool an interior space or to extract heat energy from a fluid … Energy terms