- Asymmetric fault
power engineering, specifically three phasepower, an asymmetric or unbalanced fault is a faultwhich does not affect each of the three phases equally. This is in contrast to a symmetric fault, where each of the phases is affected equally. In practice, most faults in power systems are unbalanced; however, as asymmetric faults are difficult to analyze, analysis of asymmetric faults is built up from a thorough understanding of symmetric faults.
Common types of asymmetric faults, and their causes:
* "line-to-line" - a
short circuitbetween lines, caused by ionizationof air, or when lines come into physical contact, for example due to a broken insulator.
* "line-to-ground" - a short circuit between one line and ground, very often caused by physical contact, for example due to
lightningor other stormdamage
* "double line-to-ground" - two lines come into contact with the ground (and each other), also commonly due to storm damage
An asymmetric fault breaks the underlying assumptions used in three phase power, namely that the
loadis balanced on all three phases. Consequently, it is impossible to "directly" use tools such as the one-line diagram, where only one phase is considered. However, due to the linearity of power systems, it is usual to consider the resulting voltages and currents as a superpositionof symmetrical components, to which three phase analysis can be applied.
The method of symmetric components is perhaps somewhat unintuitive, but can be verified to give correct results. The power system is seen as a superposition of three components:
* a "positive-sequence" component, in which the phases are in the same order as the original system, i.e., "a-b-c"
* a "negative-sequence" component, in which the phases are in the opposite order as the original system, i.e., "a-c-b"
* a "zero-sequence" component, which is not truly a three phase system, but instead all three phases are in phase with each other.
To determine the currents resulting from an asymmetrical fault, one must first know the per-unit zero-, positive-, and negative-sequence impedances of the transmission lines, generators, and transformers involved. Three separate circuits are then constructed using these impedances. The individual circuits are then connected together in a particular arrangement that depends upon the type of fault being studied (this can be found in most power systems textbooks). Once the sequence circuits are properly connected, the network can then be analyzed using classical circuit analysis techniques. The solution results in voltages and currents that exist as symmetrical components; these must be transformed back into phase values by using the A matrix.
* Glover, J.D., and Sarma, M.S., "Power System Analysis and Design", Brooks/Cole, 2002. (ISBN 0-534-95367-0)
* Burton, G.C., power analysis
Wikimedia Foundation. 2010.
Look at other dictionaries:
Fault — may refer to:*Fault (geology), planar rock fractures which show evidence of relative movement *Fault (technology), an abnormal condition or defect at the component, equipment, or sub system level which may lead to a failure *An asymmetric fault… … Wikipedia
Fault (technology) — In document ISO/CD 10303 226, a fault is defined as an abnormal condition or defect at the component, equipment, or sub system level which may lead to a failure. According to the Federal Standard 1037C of the United States, the term fault has the … Wikipedia
Symmetric fault — In power engineering, specifically three phase power, a symmetric, symmetrical or balanced fault is a fault which affects each of the three phases equally. In transmission line faults, roughly 5% are symmetric. This is in contrast to an… … Wikipedia
Systematic fault — Systematic faults are often a result of an error in the specification of the equipment and therefore affect all examples of that type. Such faults can remain undetected for years, until conditions conduce to create the failure. Given the same… … Wikipedia
Thrust fault — in the Qilian Shan, China. The older (left, blue and red) thrust over the younger (right, brown). A thrust fault is a type of fault, or break in the Earth s crust across which there has been relative movement, in which rocks of lower… … Wikipedia
Symmetrical components — In electrical engineering, the method of Symmetrical components is used to simplify analysis of unbalanced three phase power systems.DescriptionCharles Legeyt Fortescue in a paper presented in 1918 ( Method of Symmetrical Co Ordinates Applied to… … Wikipedia
One-line diagram — A typical one line diagram with annotated power flows. Red boxes represent circuit breakers, grey lines represent three phase bus and interconnecting conductors, the orange circle represents an electric generator, the green spiral is an inductor … Wikipedia
List of file systems — The following lists identify, characterize and link to more thorough information on computer file systems.Many older operating systems support only their one native file system, which does not bear any name apart from the name of the operating… … Wikipedia
Detachment fold — A detachment fold occurs as layer parallel thrusting along a detachment fault develops without upward propagation of a fault; the accommodation of the strain produced by thrusting results in the folding of the overlying rock units. As a visual… … Wikipedia
Shear (geology) — Study of geological shear is related to the study of structural geology, rock microstructure or rock texture and fault mechanics. Shear is the response of a rock to deformation usually by compressive stress and forms particular textures. Shear… … Wikipedia