- Hydrogen leak testing
Hydrogen leak testing is the normal way in which a
hydrogenpressure vessel or installation is checked for leaks or flaws. There are various tests.
Hydrostatic test, The vessel is filled with a nearly incompressible liquid - usually wateror oil- and examined for leaks or permanent changes in shape. The test pressure is always considerably more than the operating pressure to give a margin for safety, typically 150% of the operating pressure.
Burst test, The vessel is filled with a gas and tested for leaks. The test pressure is always considerably more than the operating pressure to give a margin for safety, typically 200% or more of the operating pressure.
*The Helium leak test, The leak detection method uses
helium(the lightest inert gas) as a tracer gas and detects it in concentrations as small as one part in 10 million. The helium is selected primarily because it penetrates small leaks readily.
* Usually a vacuum inside the object is created with an external pump connected to the instrument.
* Alternatively helium can be injected inside the product while the product itself is enclosed in a vacuum chamber connected to the instrument. In this case Burst and leakage tests can be combined in one operation.
Hydrogen microsensor, The object is filled with a mixture of 5% hydrogen/ 95% nitrogen, (below 5.7% hydrogen is non-flammable (ISO-10156). This is called typically a sniffing test. The handprobe connected to the microelectronic hydrogen sensors is used to check the object. An audiosignal increases in proximity of a leak. Detection of leaks go down to 5x10-7 cubic centimeters per second [http://www.reedlink.com/SingleArticle~ContentId~11957~pub~IA.html] . Compared to the helium test: hydrogen is cheaper than helium, no need for a vacuum, the instrument could be cheaper.
Stationairy unit, Hydrogen gas is only 7% the density of air, and thus rises. The hydrogen gas detector should be installedat the highest draft-free location in the room or compartment where hydrogen gas would accumulate.
A fixed stationary unit on the assembly line or installation. [http://www.fsec.ucf.edu/en/research/hydrogen/safety.htm Chemochromic Sensors]
Hand held testing
A light mobile point-contact sensor
Hydrogen Concentrations of 4% to 75% mixed with air (around 40,000 ppm) can be explosive.
Tracer-gas leak testing method
* [http://ej.iop.org/links/q63/,,,vhEqvhL1tjxru6ReiaQ/mst6_5_s31.pdf Fibre gratings for hydrogen sensing]
* [http://www.sandia.gov/mstc/technologies/microsensors/hydrogensensor.html Wide-Range Hydrogen Sensor]
* [http://news.ufl.edu/2006/05/24/hydrogen-sensor/ Wireless sensor]
Wikimedia Foundation. 2010.
См. также в других словарях:
Tracer-gas leak testing method — As part of the recommended leak testing methods for nondestructive testing several tracer gas leak testing ones exist among which the methods of choice are: * Helium mass spectrometer or helium leak detection, providing the highest sensitivity *… … Wikipedia
Hydrogen production — Hydrogen is commonly produced by extraction from hydrocarbon fossil fuels via a chemical path. Hydrogen may also be extracted from water via biological production in an algae bioreactor, or using electricity (by electrolysis), chemicals (by… … Wikipedia
Hydrogen technologies — are technologies that relate to the production and use of hydrogen. Hydrogen technologies are applicable for many uses.Some hydrogen technologies are carbon neutral and could have a role in preventing climate change and a possible future hydrogen … Wikipedia
Hydrogen station — A hydrogen station is a storage or filling station for hydrogen, usually located along a road or hydrogen highway, or at home as part of the distributed generation resources concept. Vehicles use hydrogen as fuel in one of several ways, including … Wikipedia
Hydrogen microsensor — A hydrogen microsensor is a gas detector that detects the presence of hydrogen. Micro fabricated point contact hydrogen sensors are used to locate leaks.Key IssuesThere are four key issues with hydrogen detectors:* Reliability: Functionality… … Wikipedia
Hydrogen compressor — A hydrogen compressor is a mechanical device that increases the pressure of hydrogen by reducing its volume. Compression of hydrogen gas naturally increases its temperature, due to Charles Law. Hydrogen embrittlement occurs.Hydrogen compressors… … Wikipedia
Hydrogen piping — For other uses, see Piping. Within installations, hydrogen piping is a system of pipes used to convey hydrogen from one location to another. For low pressure … Wikipedia
Hydrogen analyzer — A Hydrogen Analyzer is a device used to measure the amount of hydrogen concentration in steels and has industrial applications for corrosion monitoring.ee also* Hydrogen embrittlement * Hydrogen microsensor * Hydrogen leak testing … Wikipedia
Hydrogen — This article is about the chemistry of hydrogen. For the physics of atomic hydrogen, see Hydrogen atom. For other meanings, see Hydrogen (disambiguation). ← hydrogen → helium … Wikipedia
Hydrogen economy — The hydrogen economy is a proposed system of delivering energy using hydrogen. The term hydrogen economy was coined by John Bockris during a talk he gave in 1970 at General Motors (GM) Technical Center. Hydrogen advocates promote hydrogen as… … Wikipedia