- Stage pin connector
"Caution: this article discusses high and mid voltage wiring. Never work on a live circuit. If you are unsure of any electrical work consult a
licensed electrician. Articles read on wikipedia do not qualify you to work on electrical equipment.
A stage pin connector (generally known as GSP for Grounded Stage Pin) is a standard cable type for theatrical lighting in North America.
Stage pin connectors are generally used for conducting dimmed power from a
dimmerto stage lightinginstruments, although occasionally they can power other equipment.
The first stage pin connectors had two cylindrical pins, one for line (hot) and one for neutral, arranged symmetrically in a rectangular housing. The housing was milled from a solid block of
fiberglassor bakelitewhich may or may not have been impregnated with asbestosfor fire resistance plus a screw-on cover. Later connectors (including those currently being manufactured) use molded plastic housings.
These two-pin connectors were not polarized, and thus the line and neutral conductors could be exchanged depending on which way the connectors were mated. Two-pin connectors may still be found on some equipment and are often saved by electricians for wiring ungrounded fixtures (particularly
practicals), though this may or may not be advisable from a safety standpoint.
Modern stage pin connectors have incorporated a third pin for a
safety groundconnection and are commonly referred to as "2P&G" for 'two pin and ground' to distinguish them from their ungrounded two-pin predecessors. The ground pin is situated between the line and neutral pins and closer to the latter. This asymmetrical configuration effectively polarizes the connector ensuring that the line and neutral conductors are not exchanged in a properly wired installation. The ground pin is also longer than the other two, ensuring that the safety ground connection is made first when making a connection.
All stage pin connectors have longitudinal slits in the male pins that allow for compression when inserted into the female sockets to increase friction and therefore the mechanical security of the connection. A special tool appropriately called a
pin splittermay be used to expand this slit and spread the two halves of the pin to compensate for wear. A knife may be used to the same effect, but this technique risks both personal injury and damage to the connector.
For some time [http://www.unionconnector.com/ Union Connector] produced 2P&G connectors with a distinctive yellow cover that featured a locking tab in the ground pin that provided a positive mechanical lock to prevent accidental disengagement of the connectors. This design required special connectors on both the male and female side in order to work, meaning that all connectors in an installation would need to be replaced to see a real benefit to the locking feature. The expense of this proposition as well as the unpopularity of the connector itself among technicians led the locking feature to eventually be dropped, and locking connectors are no longer manufactured. The locking connectors that are still found occasionally in installations or spare parts bins are often referred to as "Union Connectors", though the Union Connector brand now features only standard non-locking stage pin connectors.
Since their introduction, stage pin connectors have been available in 20A, 30A, 60A, and 100A varieties, with the higher-current connectors being not only far larger in size but also with a different pin configuration for ground, neutral and line. Care must be taken when repairing or building these larger connectors, because Ground is on the outside pin and neutral is in the middle, with the far pin still being the line.
Most extension cables made with 20A stage pin connectors use 12/3 type SOOW or SJOOW cable which has three individually insulated 12ga (
American Wire Gauge) stranded conductors inside a larger jacket. The internal insulation is usually colored black (for line), white (for neutral) and green(for ground). This cable configuration can safely handle the full 20 Amp rating of the connector. The designation SOOW or SJOOW refers to the cable's insulation construction and type. This type of cable is very hard-wearing, resistant to oil and moisture, and resists the kinking that can result in internal conductors unlaying and twisting, which is a common problem with the SJTW cable often used in household-grade extension cords. However, older cable made using natural rubber is susceptible to dry-rotting, particularly in service in the heat generated by lighting equipment. This can cause the insulation to fail and expose or short circuitthe conductors leading to shock or fire hazard if old cable is not inspected regularly and replaced as needed.
Some stage pin extension cables may be constructed from cable with six or more conductors. This cable can be fitted with multiple stage-pin connectors at either end enabling the single cable to carry multiple independent output channels of dimmed power. Each channel or circuit should have its own line, ground, and neutral conductor independent of the other circuits, though in some cases the ground or neutral lines may be shared among circuits.
multicircuit cablesmay terminate in multicircuit connectors which may in turn be mated to panel-mount multicircuit connectors on dimming equipment or distribution boxes, other multicircuit cables (to increase length), or break-in/break-out adapters to convert the multicircuit connection to a set of stage pin connections.
The cables integrally connected to lighting instruments (often referred to as
pigtails) may use 3-conductor SJOOW or SOOW cable or individual high-temperature wires inside of a fiberglass sleeve. In the either case, the cable is often smaller gauge and sized to the current rating of the equipment it services.
Twofers are used to connect two devices to a single source. They may be constructed using individual wires inside of a fiberglass sleeve or 12/3 cable, though the latter type tends to be harder to construct and more prone to failure.
In some situations it may be desirable to connect an edison-equipped device to a stage-pin source, such as when using a household fixture as an on-stage
practical. Or it may be desirable to connect a stage pin-equipped device to an edison source, such as when using theatrical equipment for architectural or retail displays. In either case adapters may be constructed with a female edison connector and a male stage pin connector or vice versa.
Note: It is not advisable to use fluorescent fixtures on dimmers unless the dimming equipment is manufacturer-specified to power fluorescent fixtures and/or the fixture is fitted with a dimmable ballast. Many modern dimming systems can set dimming profiles on a per-channel basis to, among other purposes, control fluorescent fixtures.
Some facilities feature 60 or 100 Amp circuits which have larger versions of the stage pin connector to match the higher current rating. Since it is unusual to require more than 20 Amps on a single circuit with modern lighting equipment, adapters may be made to convert a single 60 or 100 Amp stage pin connection to 3-5 20 Amp stage pin connections. However, each downstream connection must be independently protected by a fuse or breaker to avoid exceeding the current rating of downstream cables and connectors.
tage pin versus NEMA 5-15 (Edison) Connectors
The primary advantage of the stage pin connector over the
NEMA5-15 connector (commonly known as an Edison plug) is its increased durability and resistance to damage due to its more robust construction and the ability to compensate for wear with a pin splitter. Having a distinct connector designated for dimmable power also helps prevent confusion of dimmed and non-dimmed circuits which could lead to equipment damage. Even the smallest stage pin connectors are rated for 20A, which translates to 2.4kW at 120 Volts, compared to the 15A and 1.8kW of the NEMA 5-15.
Despite the advantages of stage pin connectors, many smaller installations use Edison connectors due to their availability and the ease of connecting equipment to outlets already available in a building. This reduces refit costs, particularly when small portable dimming packs (often 4x 1.2kW channel models) are used. Such installations may also use inexpensive store-bought extension cables, though care must be taken to ensure that the ratings of such extension cables are not exceeded.
Though the initial cost of constructing a 12/3 stage pin extension cable is higher than simply purchasing an equivalent edison extension cable, the maintenance costs of the former are ultimately lower for several reasons. To begin with, less maintenance will be required as a result of the more rugged construction. When maintenance is required, many cable faults may be repaired by disassembling the connector, replacing broken components with spares acquired by cannibalizing other broken connectors, trimming away defective sections of cable, and reapplying the connector to the cable. This sort of repair is not usually possible with edison connectors, particularly the factory-molded type. If a connector is beyond repair, a new stage pin connector is often less expensive than a replacement edison connector when purchased from local vendors.
Though stage pin connectors are usually used in part to distinguish dimmed circuits from non-dimmed edison circuits, newer theatrical installations may have several dimmed circuits that terminate in edison outlets at various locations for convenience; thus care must be taken to avoid using these circuits for non-dimmable equipment. Connecting certain non-dimmable appliances or equipment to dimmed circuits may result in damage to the dimming equipment or the downstream device.
Most modern stage pin connectors feature a ground pin that is longer than the line and neutral pins, ensuring that the ground connection is made first, and thus the
safety groundis in place before line voltage is applied to the downstream equipment.
As an added precaution, some SPCs are built with a clear housing on one side. This allows a user to confirm that they are wired correctly before connecting them.
On some older female pin receptacles, the actual electrical contacts are not very deeply recessed in the plug body and can easily be accidentally contacted resulting in an electric shock if the circuit is live. This was one advantage of the Edison outlet in that it was impossible to contact live parts unless something conductive was inserted into the slots. New connectors have addressed this problem by mounting the contacts deeper inside the connector body so they cannot be accidentally contacted.
A major disadvantage to the design of this style of connector is that it is possible to mate the connectors with one reversed such that the ground pin is inserted into the line socket and the line pin is inserted into the ground socket. For equipment mechanically attached to grounded building structures such as a lighting instrument mounted to a batten or grid this will cause a line-ground short circuit. For equipment not attached to a building ground, such as a floor-mounted lighting instrument, this condition will cause the chassis of the equipment to become electrified creating a shock hazard. Care must therefore be taken to avoid misaligning plugs. It is also possible to mate stage pin connectors such that the ground pin is inserted into the neutral socket and the neutral pin is inserted into the ground socket, but this mistake does not usually result in a fault condition unless there is a hot-neutral reverse upstream in the cabling.
Stage pin connectors are specified by
United States Institute for Theatre Technologystandard "USITT S3-1997 Standard for Stage Pin Connectors."
Other Connectors Used in Theatre Applications
Many theatres also use
Edison plugs/connectors, which is the standard connector used in homes and businesses in North America, because of their availability and the ability to connect household fixtures to a theatrical control system. Twist-lock connectors are used in many theatres because of their locking feature, which will not allow fixtures to become accidentally disconnected. It is important to note that all connectors used to power lighting fixtures must be rated at 20 amps or higher, depending on local electrical codes. Temporary high-power distribution wiring often employs Camlockconnectors to connect dimming equipment, Power Distribution Units, controllers for motorized Chain Hoists, and other high-power equipment to a Company Switch, generator, or other tie-in point.UK theatrical lighting installations normally use the BS 546 type plug rated at 15A (The higher phase voltage of 230V allows lower currents for the same power) or occasionally IEC 6030916A industrial Plugs. Most Dimmer racks also use IEC 60309 32A or 63A plugs on the non dimmed side.
* http://www.usitt.org/bookstore/downloads/U87%20S3-StgPinStandard20050610.pdf(This is standard defined by the
USITTand a source for this article)
Wikimedia Foundation. 2010.
Look at other dictionaries:
XLR connector — The XLR connector is an electrical connector design. XLR plugs and sockets are used mostly in professional audio and video electronics cabling applications. Home audio and video electronics normally use RCA connectors. In reference to its… … Wikipedia
Fly system — Fly loft of the Theater Bielefeld in Germany A fly system, flying system or theatrical rigging system, is a system of lines (e.g. ropes), blocks (pulleys), counterweights and related devices within a theatre that enable a stage crew to quickly,… … Wikipedia
AC power plugs and sockets — See also: Industrial and multiphase power plugs and sockets Plugs and sockets may sometimes combine male and female contacts, but t … Wikipedia
Parabolic aluminized reflector light — A Parabolic Aluminized Reflector luminaire 20 PAR cans A parabolic aluminized refle … Wikipedia
Intelligent lighting — A Martin MAC 550 intelligent light Intelligent lighting refers to stage lighting that has automated or mechanical abilities beyond those of traditional, stationary illumination. Although the most advanced intelligent lights can produce… … Wikipedia
Color scroller — A color scroller or color changer is an electro mechanical lighting accessory used in theater, film, dance and concerts to change the color projected by stage lighting instruments without the need of a person to be in the vicinity of the light. A … Wikipedia
Outline of stagecraft — Stagecraft is a generic term referring to the technical aspects of theatrical, film, and video production. Stagecraft is distinct from the wider umbrella term of scenography. Considered a technical rather than an artistic field, it relates… … Wikipedia
Theatrical property — Props set the mood for the musical number Food, Glorious Food in the musical production, Oliver A theatrical property, commonly referred to as a prop, is an object used on stage by actors to further the plot or story line of a theatrical… … Wikipedia
Cyclorama (theater) — A band performing in front of a cyclorama. A gobo has been projected on it and it is washed with blue gelled lights A cyclorama is a large curtain or wall, often concave, positioned at the back of the stage area. It was popularized in the German… … Wikipedia
Gobo (lighting) — For other uses, see Gobo (disambiguation). A gobo in a gobo holder, which goes in a stage lighting instrument. The discolored portion is oxidation of the stainless steel caused by the high temperature of the lamp, but the gobo is still usable. A… … Wikipedia