- Electrical bonding
Electrical bonding is the practice of intentionally electrically connecting all metallic non-current carrying items in a room or building as protection from
electric shock. If a failure of electrical insulation occurs, all metal objects in the room will have the same electrical potential, so that an occupant of the room cannot touch two objects with significantly different potentials. Even if the connection to a distant earth ground is lost, the occupant will be protected from dangerous potential differences.
Bonding refers to the fact that in a building with
electricityit is normal for safetyreasons to connect all metalobjects such as pipes together to the mains earthto form an equipotential zone. This is done in the UK because many buildings are supplied with a single phasesupply cablewhere the neutral and earth conductors are combined. Close to the electricity meterthis conductor is divided into two, the "earth" terminal and the wire going to the neutral busbarin the consumer unit. In the event of a break in a neutral connection this "earth" terminal provided by the supply companywill be at a potential (relative to the true earth) which is the same as the live wire (phase wire) coming to the home.
Examples of articles that may be bonded include metallic water piping systems, gas piping, ducts for central heating and air conditioing systems, and exposed metal parts of buildings such as hand rails, stairs, ladders, platforms and floors.
If a person was to touch the metal (earthed casing) of an electrical device during the a fault condition and be in contact with a metal object connected to a remote earth then they would get an
electric shock. If all metal objects are connected together, all the metal objects in the building will be at the same potential. It then will not be possible to get a shock by touching two 'earthed' objects at once.
Bonding is particularly important for swimming pools and fountains. In pools and fountains, any metallic object (other than conductors of the power circuit)over a certain size must be bonded to assure that all conductors are equipotential and do not provide a hazardous conductive path. SInce is is buried in the ground, a pool can be a better ground than the electric panel ground. With all the conducting elements bonded, it is less likely that electric current will find a path through a swimmer. In concrete pools even the reinforcing bars of the concrete must be connected to the bonding system to ensure no dangerous potential gradients are produced during a fault.
How the earth protects
In a system with a grounded (earthed) neutral, connecting all non-current-carrying metallic parts of equipment to earth ground at the main service panel, will ensure that current due to faults (such as a "hot" wire touching the frame or chassis of the device) will be diverted to earth. In a TN system where there is a direct connection from the installation earth to the transformer neutral, earthing will allow the branch circuit overcurrent protection (a fuse or
circuit breaker) to detect the fault rapidly and interrupt the circuit. In the case of a TT system where the impedance is high due to the lack of direct connection to the transformerneutral, an RCD (Residual-Current Device, sometimes known as a Residual Current Circuit Breaker or Ground Fault Circuit Interrupter) must be used to provide disconnection. RCDs are also used in other situations where rapid disconnection of small earth faults (including a human touching a live wire by accident, or damage) is desired.
Equipotential bonding involves joining together metalwork that is or may be earthed so that it is at the same
potential(i.e., voltage) everywhere. Such is commonly used under transformer banks by power companies and under large computer installations. Equipotential bonding is done from the Service Panel consumer unit(also known as a fuse box, breaker box, or distribution board) to incoming waterand gasservices. It is also done in bathroomswhere all exposed metal that leaves the bathroom including metal pipesand the earths of electrical circuits must be bonded together to ensure that they are always at the same potential. Isolated metal objects including metal fittings fed by plastic pipe (water in a thin pipe is actually a very poor conductor) are not required to be bonded. European and North American practices differ here; equipotential bonding in bathrooms is not required by North American codes, although it is required around swimming_pools. In Australiaand South Africa, a house's earth cables must be connected both to an earthing rod/stake driven into the ground and also to the plumbing. Exact rules for electrical installations vary by country, locality, or supplying power company.
Earth potential rise
Wikimedia Foundation. 2010.
Look at other dictionaries:
Electrical conduit — risers, seen inside fire resistance rated shaft, as seen entering bottom of a firestop. The firestop is made of firestop mortar on top, rockwool on the bottom. Raceways are used to protect cables from damage … Wikipedia
Electrical wiring (United States) — Electrical wiring in general refers to conductors used to carry electricity and their accessories. General aspects of electrical wiring as used to provide power in or to buildings and structures, commonly referred to as building wiring, are… … Wikipedia
Electrical wiring — in general refers to insulated conductors used to carry electricity, and associated devices. This article describes general aspects of electrical wiring as used to provide power in buildings and structures, commonly referred to as building wiring … Wikipedia
Bonding jumper — A bonding jumper is a reliable conductor to ensure the required electrical conductivity between metal parts required to be electrically connectedcite book | last = edited by Robert H. Griffin | title = Safety and Health Requirements Manual: U. S … Wikipedia
bonding — In electrical engineering, the process of connecting together metal parts so that they make low resistance electrical contact for direct current and lower frequency alternating currents. See also earthing … Military dictionary
bonding jumper — noun An electrical connection that bonds the electrical supply to ground via the water piping system … Wiktionary
bonding — The act of connecting all metal parts of the aircraft to secure good electrical continuity and so avoid the undesirable effects of static electricity … Aviation dictionary
chemical bonding — ▪ chemistry Introduction any of the interactions that account for the association of atoms into molecules, ions, crystals, and other stable species that make up the familiar substances of the everyday world. When atoms approach one another … Universalium
Ball bonding — is a type of wire bonding, and is the most common way to make the electrical interconnections between a microchip and the outside world as part of semiconductor device fabrication.Gold or copper wire can be used, though gold is more common… … Wikipedia
Canadian Electrical Code — The Canadian Electrical Code, CE code, or CSA C22.1 code is a standard published by the Canadian Standards Association for addressing electrical safety, shock, and fire hazards of electrical products in Canada. The Council for the Harmonization… … Wikipedia