- Programmable logic controller
A programmable logic controller (PLC) or programmable controller is a
digital computerused for automationof industrial processes, such as control of machinery on factory assembly lines. PLCs are used in many different industries and machines such as packaging and semiconductor machines. Unlike general-purpose computers, the PLC is designed for multiple inputs and output arrangements, extended temperature ranges, immunity to electrical noise, and resistance to vibration and impact. Programs to control machine operation are typically stored in battery-backed or non-volatile memory. A PLC is an example of a real time system since output results must be produced in response to input conditions within a bounded time, otherwise unintended operation will result.
The main difference from other computers is that PLCs are armored for severe conditions (dust, moisture, heat, cold, etc) and have the facility for extensive
input/output(I/O) arrangements. These connect the PLC to sensors and actuators. PLCs read limit switches, analog process variables (such as temperature and pressure), and the positions of complex positioning systems. Some even use machine vision. On the actuator side, PLCs operate electric motors, pneumaticor hydrauliccylinders, magnetic relays or solenoids, or analog outputs. The input/output arrangements may be built into a simple PLC, or the PLC may have external I/O modules attached to a computer network that plugs into the PLC.
A small PLC will have a fixed number of connections built in for inputs and outputs. Typically, expansions are available if the base model does not have enough I/O.
Modular PLCs have a chassis (also called a rack) into which is placed modules with different functions. The processor and selection of I/O modules is customised for the particular application. Several racks can be administered by a single processor, and may have thousands of inputs and outputs. A special high speed serial I/O link is used so that racks can be distributed away from the processor, reducing the wiring costs for large plants.
PLCs may need to interact with people for the purpose of configuration, alarm reporting or everyday control.
A Human-Machine Interface (HMI) is employed for this purpose. HMI's are also referred to as MMI's (Man Machine Interface) and GUI (Graphical User Interface). A simple system may use buttons and lights to interact with the user. Text displays are available as well as graphical touch screens.
List of human-computer interaction topics
PLCs have built in communications ports usually 9-Pin
RS232, and optionally for RS485and Ethernet. Modbusor DF1is usually included as one of the communications protocols. Others' options include various fieldbuses such as DeviceNetor Profibus. Other communications protocols that may be used are listed in the List of automation protocols.
Most modern PLCs can communicate over a network to some other system, such as a computer running a
SCADA(Supervisory Control And Data Acquisition) system or web browser.
PLCs used in larger I/O systems may have peer-to-peer (P2P) communication between processors. This allows separate parts of a complex process to have individual control while allowing the subsystems to co-ordinate over the communication link. These communication links are also often used for HMI (Human-Machine Interface) devices such as keypads or PC-type workstations. Some of today's PLCs can communicate over a wide range of media including RS-485, Coaxial, and even
Ethernetfor I/O control at network speeds up to 100 Mbit/s.
PICs are well-adapted to a range of tasks. These are typically industrial processes in manufacturing where the cost of developing and maintaining the automation system is high relative to the total cost of the automation, and where changes to the system would be expected during its operational life. PICs contain input and output devices compatible with industrial pilot devices and controls; little electrical design is required, and the design problem centers on expressing the desired sequence of operations in
ladder logic(or function chart) notation. PIC applications are typically highly customized systems so the cost of a packaged PIC is low compared to the cost of a specific custom-built controller design. On the other hand, in the case of mass-produced goods, customized control systems are economic due to the lower cost of the components, which can be optimally chosen instead of a "generic" solution, and where the non-recurring engineering charges are spread over thousands or millions of units.
For high volume or very simple fixed automation tasks, different techniques are used. For example, a consumer
dishwasherwould be controlled by an electromechanical cam timercosting only a few dollars in production quantities.
microcontroller-based design would be appropriate where hundreds or thousands of units will be produced and so the development cost (design of power supplies and input/output hardware) can be spread over many sales, and where the end-user would not need to alter the control. Automotive applications are an example; millions of units are built each year, and very few end-users alter the programming of these controllers. However, some specialty vehicles such as transit busses economically use PICs instead of custom-designed controls, because the volumes are low and the development cost would be uneconomic.
Very complex process control, such as used in the chemical industry, may require algorithms and performance beyond the capability of even high-performance PLCs. Very high-speed or precision controls may also require customized solutions; for example, aircraft flight controls.
PICs may include logic for single-variable feedback analog control loop, a "proportional, integral, derivative" or "
PID controller." A PID loop could be used to control the temperature of a manufacturing process, for example. Historically PLCs were usually configured with only a few analog control loops; where processes required hundreds or thousands of loops, a distributed control system(DCS) would instead be used. However, as PLCs have become more powerful, the boundary between DCS and PLC applications has become less clear-cut.
PLCs have similar functionality as
Remote Terminal Units. An RTU, however, usually does not support control algorithms or control loops. As hardware rapidly becomes more powerful and cheaper, PICs and DCS's are increasingly beginning to overlap in responsibilities, and many vendors sell RTUs with PIC-like features and vice versa. The industry has standardized on the IEC 61131-3 functional block language for creating programs to run on RTUs and PICs, although nearly all vendors also offer proprietary alternatives and associated development environments.
Digital and analog signals
Digital or discrete signals behave as binary switches, yielding simply an On or Off signal (1 or 0, True or False, respectively). Push buttons, limit switches, and
photoelectric sensors are examples of devices providing a discrete signal. Discrete signals are sent using either voltageor current, where a specific range is designated as "On" and another as "Off". For example, a PLC might use 24 V DC I/O, with values above 22 V DC representing "On", values below 2VDC representing "Off", and intermediate values undefined. Initially, PLCs had only discrete I/O.
Analog signals are like volume controls, with a range of values between zero and full-scale. These are typically interpreted as integer values (counts) by the PLC, with various ranges of accuracy depending on the device and the number of bits available to store the data. As PLCs typically use 16-bit signed binary processors, the integer values are limited between -32,768 and +32,767. Pressure, temperature, flow, and weight are often represented by analog signals. Analog signals can use
voltageor current with a magnitude proportional to the value of the process signal. For example, an analog 4-20 mAor 0 - 10 V input would be converted into an integer value of 0 - 32767.
Current inputs are less sensitive to electrical noise (i.e. from welders or electric motor starts) than voltage inputs.
As an example, say a facility needs to store water in a tank. The water is drawn from the tank by another system, as needed, and our example system must manage the water level in the tank.
Using only digital signals, the PLC has two digital inputs from
float switches (Low Level and High Level). When the water level is above the switch it closes a contact and passes a signal to an input. The PLC uses a digital output to open and close the inlet valveinto the tank.
When the water level drops enough so that the Low Level float switch is off (down), the PLC will open the valve to let more water in. Once the water level raises enough so that the High Level switch is on (up), the PLC will shut the inlet to stop the water from overflowing. This rung is an example of seal in logic. The output is sealed in until some condition breaks the circuit.
Low Level High Level Fill Valve
------ [/] ------|------ [/] ----------------------(OUT)---------
Fill Valve |
------ [ ] ------|
An analog system might use a water
pressure sensoror a load cell, and an adjustable (throttling)dripping out of the tank, the valve adjusts to slowly drip water back into the tank.
In this system, to avoid 'flutter' adjustments that can wear out the valve, many PLCs incorporate "
hysteresis" which essentially creates a " deadband" of activity. A technician adjusts this deadband so the valve moves only for a significant change in rate. This will in turn minimize the motion of the valve, and reduce its wear.
A real system might combine both approaches, using float switches and simple valves to prevent spills, and a rate sensor and rate valve to optimize refill rates and prevent
water hammer. Backup and maintenance methods can make a real system very complicated.
PLC programs are typically written in a special application on a personal computer, then downloaded by a direct-connection cable or over a network to the PLC. The program is stored in the PLC either in battery-backed-up
RAMor some other non-volatile flash memory. Often, a single PLC can be programmed to replace thousands of relays.
IEC 61131-3standard, PLCs can be programmed using standards-based programming languages. A graphical programming notation called Sequential Function Charts is available on certain programmable controllers.
Recently, the International standard
IEC 61131-3has become popular. IEC 61131-3 currently defines five programming languages for programmable control systems: FBD ( Function block diagram), LD (Ladder diagram), ST ( Structured text, similar to the Pascal programming language), IL ( Instruction list, similar to assembly language) and SFC ( Sequential function chart). These techniques emphasize logical organization of operations.
While the fundamental concepts of PLC programming are common to all manufacturers, differences in I/O addressing, memory organization and instruction sets mean that PLC programs are never perfectly interchangeable between different makers. Even within the same product line of a single manufacturer, different models may not be directly compatible.
The PLC was invented in response to the needs of the American automotive manufacturing industry. Programmable controllers were initially adopted by the automotive industry where software revision replaced the re-wiring of hard-wired control panels when production models changed.
Before the PLC, control, sequencing, and safety interlock logic for manufacturing automobiles was accomplished using hundreds or thousands of
relays, cam timers, and drum sequencers and dedicated closed-loop controllers. The process for updating such facilities for the yearly model change-over was very time consuming and expensive, as the relay systems needed to be rewired by skilled electricians.
In 1968 GM Hydramatic (the automatic transmission division of
General Motors) issued a request for proposal for an electronic replacement for hard-wired relay systems.
The winning proposal came from Bedford Associates of
Bedford, Massachusetts. The first PLC, designated the 084 because it was Bedford Associates' eighty-fourth project, was the result. Bedford Associates started a new company dedicated to developing, manufacturing, selling, and servicing this new product: Modicon, which stood for MOdular DIgital CONtroller. One of the people who worked on that project was Dick Morley, who is considered to be the "father" of the PLC. The Modicon brand was sold in 1977 to Gould Electronics, and later acquired by German Company AEGand then by French Schneider Electric, the current owner.
One of the very first 084 models built is now on display at Modicon's headquarters in
North Andover, Massachusetts. It was presented to Modicon by GM, when the unit was retired after nearly twenty years of uninterrupted service.
The automotive industry is still one of the largest users of PLCs, and Modicon still numbers some of its controller models such that they end with eighty-four.
Early PLCs were designed to replace relay logic systems. These PLCs were programmed in "
ladder logic", which strongly resembles a schematic diagram of relay logic. Modern PLCs can be programmed in a variety of ways, from ladder logic to more traditional programming languages such as BASIC and C. Another method is State Logic, a Very High Level Programming Languagedesigned to program PLCs based on State Transition Diagrams.
Many of the earliest PLCs expressed all decision making logic in simple
ladder logicwhich appeared similar to electrical schematic diagrams. The electricians were quite able to trace out circuit problems with schematic diagrams using ladder logic. This program notation was chosen to reduce training demands for the existing technicians. Other early PLCs used a form of instruction listprogramming, based on a stack-based logic solver.
Early PLCs, up to the mid-1980s, were programmed using proprietary programming panels or special-purpose programming terminals, which often had dedicated function keys representing the various logical elements of PLC programs. Programs were stored on cassette tape cartridges. Facilities for printing and documentation were very minimal due to lack of memory capacity. The very oldest PLCs used non-volatile
magnetic core memory.
The functionality of the PLC has evolved over the years to include sequential relay control, motion control,
process control, distributed control systems and networking. The data handling, storage, processing power and communication capabilities of some modern PLCs are approximately equivalent to desktop computers. PLC-like programming combined with remote I/O hardware, allow a general-purpose desktop computer to overlap some PLCs in certain applications.
Well known PLC brands are Siemens,
Allen-Bradley, IDEC, ABB, Mitsubishi, Omron, Schneider Electricand General Electric.
* [http://www.electronicspal.com/plc/ PLC Complete Tutorial]
* [http://www.plcs.net/contents.shtml Beginners PLC Primer]
* [http://www.ccontrols.com/pdf/Extv4n2.pdf Interview with Dick Morley (pdf)]
* [http://plc.sourceforge.net/ Linux PLC directory]
* [http://www.plctutor.com/ PLC Tutor]
* [http://claymore.engineer.gvsu.edu/~jackh/books/plcs/powerpoint/ch01.ppt Power Point on PLC Ladder Logic]
* [http://www.artikel-software.com/blog/2007/06/17/plc-programmable-logic-controller/ PLC books pdf]
* [http://thelearningpit.com/ The Learning Pit - PLC Tutor ]
* [http://www.plcmanual.com/ PLC Basics]
Wikimedia Foundation. 2010.
Look at other dictionaries:
Programmable logic controller — Automate programmable industriel Pour les articles homonymes, voir API. Deux automates programmables Industriels leurs périphériques, m … Wikipédia en Français
Programmable Logic Controller — Rack mit einer Speicherprogrammierbaren Steuerung Eine Speicherprogrammierbare Steuerung (SPS, engl. Programmable Logic Controller, PLC) ist eine Baugruppe, die zur Steuerung oder Regelung einer Maschine oder Anlage eingesetzt wird. In der Regel… … Deutsch Wikipedia
Programmable logic controller — Rack mit einer Speicherprogrammierbaren Steuerung Eine Speicherprogrammierbare Steuerung (SPS, engl. Programmable Logic Controller, PLC) ist eine Baugruppe, die zur Steuerung oder Regelung einer Maschine oder Anlage eingesetzt wird. In der Regel… … Deutsch Wikipedia
programmable logic controller — programuojamasis loginis valdiklis statusas T sritis automatika atitikmenys: angl. PLC; programmable logic controller vok. PLC; programmierbare Verknüpfungssteuerung, f rus. программируемый логический контроллер, m pranc. contrôleur logique… … Automatikos terminų žodynas
programmable logic controller — noun A programmable electronic device used in industrial automation to provide logic and sequencing controls for machinery … Wiktionary
programmable logic controller — noun → PLC1. Also, programmable controller … Australian English dictionary
Programmable automation controller — A programmable automation controller (PAC) is a compact controller that combines the features and capabilities of a PC based control system with that of a typical programmable logic controller (PLC). Therefore, the PAC features not only… … Wikipedia
Programmable logic device — A programmable logic device or PLD is an electronic component used to build reconfigurable digital circuits. Unlike a logic gate, which has a fixed function, a PLD has an undefined function at the time of manufacture. Before the PLD can be used… … Wikipedia
Programmable controller — may be: * Programmable logic controller * Programmable automation controller * Programmable Interrupt Controller * Universal remote … Wikipedia
Controller (computing) — In computing and especially in computer hardware, controller is a chip, an expansion card, or a stand alone device (usually called a control unit) that interfaces with a peripheral device. This may be a link between two parts of a computer (for… … Wikipedia