- Chilled water
Chilled water is a commodity often used to cool a building's air and equipment, especially in situations where many individual rooms must be controlled separately, such as a hotel. The chilled water can be supplied by a vendor, such as a public utility or created at the location of the building that will use it, which has been the norm.
Chilled water cooling is very different from typical residential air conditioning where a refrigerant is pumped through an air handler to cool the air.
Regardless of who provides it, the chilled water (between 4° and 7°C) is pumped through an air handler, which captures the heat from the air, then disperses the air throughout the area to be cooled.
The condenser water absorbs heat from the refrigerant in the condenser barrel of the water chiller, and is then sent via return lines to a cooling tower, which is a heat exchange device used to transfer waste heat to the atmosphere. The extent to which the cooling tower decreases the temperature depends upon the outside temperature, the relative humidity and the atmospheric pressure. The water in the chilled water circuit will be lowered to the Wet-bulb temperature or dry-bulb temperature before proceeding to the water chiller, where it is cooled to between 4° and 7°C and pumped to the air handler, where the cycle is repeated. The equipment required includes chillers, cooling towers, pumps and electrical control equipment. The initial capital outlay for these is substantial and maintenance costs can fluctuate. Adequate space must be included in building design for the physical plant and access to equipment.
The chilled water, which absorbed heat from the air, is sent via return lines back to the utility facility, where the process described in the previous section occurs. Utility generated chilled water eliminates the need for chillers and cooling towers at the property, reduces capital outlays and eliminates ongoing maintenance costs. The physical space saved can also become rentable, increasing revenue.
Utility supplied chilled water has been used successfully since the 1960’s in many cities, and technological advances in the equipment, controls and trenchless installation have increased efficiency and lowered costs.
The advantage of utility-supplied chilled water is based on economy of scale. A utility can operate one large system more economically than a customer can operate the individual system in one building. The utility's system also has back-up capacity to protect against sudden outages. The cost of such "insurance" is also markedly lower than what it would be for an individual structure.
The use of utility supplied chilled water is most cost effective when it is designed into the building’s infrastructure or when chiller/cooling tower equipment must be replaced. Commercial customers often lower their air conditioning costs from 10-20% by purchasing chilled water.
Wikimedia Foundation. 2010.
Look at other dictionaries:
chilled water stowage — storing commercial fish in chilled fresh or salt water using ice or mechanical refrigeration. Limited to about 3 4 days as some fish take up water and salt, their eyes become cloudy and gills are bleached as blood is lost … Dictionary of ichthyology
Chilled-water system — Станция водоохлаждения (для рулонной офсетной печати) … Краткий толковый словарь по полиграфии
District chilled water — Chilled water from an outside source used as an energy source for cooling in a building. The water is chilled in a central plant and piped into the building. Chilled water may be purchased from a utility or provided by a central physical plant… … Energy terms
Water cooler — A water cooler (commonly spelled watercooler as a compound word) is a device that cools and dispenses water. They are generally broken up in two categories: bottle less and bottled water coolers. Bottle less water coolers are hooked up to a water … Wikipedia
Water detector — A Water detector is a small electronic device that is designed to detect the presence of water and alert humans in time to allow the prevention of water damage. A common design is a small device that lays flat on a floor and relies on the… … Wikipedia
Chilled — EP by Chicane Released 16 August 1999 … Wikipedia
Water ice — can refer to: *Ice, frozen water *A chilled snack similar to Italian Ice … Wikipedia
water-cooled — chilled by water … English contemporary dictionary
Chilled beam — A chilled beam is a type of convection HVAC system designed to heat or cool large buildings. Pipes of water are passed through a beam (a heat exchanger) suspended a short distance from the ceiling of a room. As the beam chills the air… … Wikipedia
chilled — adj. VERBS ▪ be, feel ▪ I suddenly felt chilled and had to go indoors. ▪ serve sth ▪ The wine is best served chilled. PHRASES … Collocations dictionary