- Log mean temperature difference
The

**log mean temperature difference**(LMTD) is used to determine the temperature driving force for heat transfer in flow systems (most notably inheat exchanger s). The LMTD is a logarithmic average of the temperature difference between the hot and cold streams at each end of the exchanger. The use of the LMTD arises straightforwardly from the analysis of a heat exchanger with constant flow rate and fluid thermal properties.For

Countercurrent flow (i.e. where the hot stream, liquid or gas, goes from say left to right, and the cold stream, again liquid or gas goes from right to left), is given by the following equation::$LMTD=frac\{(T\_1-t\_2)-(T\_2-t\_1)\}\{lnfrac\{(T\_1-t\_2)\}\{(T\_2-t\_1)$

And for

Parallel flow (i.e. where the hot stream,nliquid or gas, goes from say left to right, and so does the cold stream), is given by the following equation::$LMTD=frac\{(T\_1-t\_1)-(T\_2-t\_2)\}\{lnfrac\{(T\_1-t\_1)\}\{(T\_2-t\_2)$

:$T\_1=$Hot Stream Inlet Temp. :$T\_2=$Hot Stream Outlet Temp.

:$t\_1=$Cold Stream Inlet Temp. :$t\_2=$Cold Stream Outlet Temp.

It makes no difference which temperature differential is 1 or 2 as long as the nomenclature is consistent.The larger the LMTD, the more heat is transferred.

Yet a third type of unit is a cross-flow exchanger, in which one system (usually the heat sink) has the same nominal temperature at all points on the heat transfer surface. This follows similar mathematics, in its dependence on the LMTD, except that a correction factor F often needs to be included in the heat transfer relationship.

There are times when the four temperatures used to calculate the LMTD are not available, and the

NTU method may then be preferable.**Derivation**Assume heat transfer is occurring between two fluids ($T\_1$ and $T\_2$) with a temperature "difference" of $Delta\; T(A)$ at point A and $Delta\; T(B)$ at point B (where $Delta\; T(z)=T\_2(z)-T\_1(z)$). The direction of fluid flow does not need to be considered. Since LMTD is the "average" temperature difference of the two streams between points A and B the following formula defines LMTD:

:$LMTD=frac\{int^\{B\}\_\{A\}\; Delta\; T(z),dz\}\{int^\{B\}\_\{A\},dz\}$ where $z$ is the distance parallel to the motion of the two fluids.

The rate of change of the temperature of the two fluids, $T\_1$ and $T\_2$ respectively, is proportional to the temperature difference between the two fluids:

:$frac\{dT\_1\}\{dz\}=k\_a\; (T\_1(z)-T\_2(z))=-k\_aDelta\; T(z)$

:$frac\{dT\_2\}\{dz\}=k\_b\; (T\_2(z)-T\_1(z))=k\_bDelta\; T(z)$

Therefore:

:$frac\{d(Delta\; T)\}\{dz\}=frac\{d(T\_2-T\_1)\}\{dz\}=frac\{dT\_2\}\{dz\}-frac\{dT\_1\}\{dz\}=KDelta\; T(z)$ where $K=k\_a+k\_b$

This gives us a value for $dz$:

:$dz=frac\{1\}\{K\},frac\{d(Delta\; T)\}\{Delta\; T\}$

Substituting back into our formula for LMTD:

:$LMTD=frac\{int^\{B\}\_\{A\}\; Delta\; T(z),dz\}\{int^\{B\}\_\{A\},dz\}=frac\{int^\{Delta\; T(B)\}\_\{Delta\; T(A)\}\; frac\{1\}\{K\},d(Delta\; T)\}\{int^\{Delta\; T(B)\}\_\{Delta\; T(A)\}\; frac\{1\}\{K\},frac\{d(Delta\; T)\}\{Delta\; T$

Integrating gives:

:$LMTD=frac\{int^\{Delta\; T(B)\}\_\{Delta\; T(A)\}\; frac\{1\}\{K\},d(Delta\; T)\}\{int^\{Delta\; T(B)\}\_\{Delta\; T(A)\}\; frac\{1\}\{K\},frac\{d(Delta\; T)\}\{Delta\; T=frac\{Delta\; T]\; ^\{Delta\; T(B)\}\_\{Delta\; T(A)\{ln\{Delta\; T\}]\; ^\{Delta\; T(B)\}\_\{Delta\; T(A)=frac\{Delta\; T(B)-Delta\; T(A)\}\{ln(frac\{Delta\; T(B)\}\{Delta\; T(A)\})\}$

Trivial case:

:$\{Delta\; T(z)\; =\; C\}$ for all $z$

:$LMTD=frac\{int^\{B\}\_\{A\}\; Delta\; T(z),dz\}\{int^\{B\}\_\{A\},dz\}=frac\{Cint^\{B\}\_\{A\},dz\}\{int^\{B\}\_\{A\},dz\}=C$

**Assumptions**It has been assumed that the rate of change for the temperature of both fluids is proportional to the temperature difference; this assumption is valid for fluids with a constant

specific heat , which is a good description of fluids changing temperature over a relatively small range. However, if the specific heat changes, the LMTD approach will no longer be accurate.A particular case where the LMTD is not applicable are condensers and

reboiler s, where thelatent heat associated to phase change makes the hypothesis invalid.**References**Kay J M & Nedderman R M (1985) "Fluid Mechanics and Transfer Processes", Cambridge University Press

**External links**Simple LMTD calculator: http://www.fridgetech.com/calculators/lmtd2.html

Advanced LMTD calculator: http://www.chemsof.com/lmtd/lmtd.htm

*Wikimedia Foundation.
2010.*

### Look at other dictionaries:

**Heat exchanger**— An interchangeable plate heat exchanger Tubular heat exchan … Wikipedia**Heat transfer**— is a discipline of thermal engineering that concerns the exchange of thermal energy from one physical system to another. Heat transfer is classified into various mechanisms, such as heat conduction, convection, thermal radiation, and phase change … Wikipedia**Heat transfer coefficient**— The heat transfer coefficient, in thermodynamics and in mechanical and chemical engineering, is used in calculating the heat transfer, typically by convection or phase change between a fluid and a solid::Delta Q=h cdot A cdot Delta T cdot Delta… … Wikipedia**NTU method**— The Number of Transfer Units (NTU) Method is used to calculate the rate of heat transfer in heat exchangers (especially counter current exchangers) when there is insufficient information to calculate the Log Mean Temperature Difference (LMTD). In … Wikipedia**Concentric tube heat exchanger**— Concentric Tube (or Pipe) Heat Exchangers are used in a variety of industries for purposes such as material processing, food preparation and air conditioning.[1] They create a temperature driving force by passing fluid streams of different… … Wikipedia**Shell and tube heat exchanger**— A shell and tube heat exchanger is a class of heat exchanger designs. [ cite book|author=Sadik Kakaç and Hongtan Liu|title=Heat Exchangers: Selection, Rating and Thermal Design|edition=2nd Edition|publisher=CRC Press|year=2002|id=ISBN 0849309026] … Wikipedia**Reaction calorimeter**— A reaction calorimeter is an instrument that enables the energy being released or absorbed by a reaction to be measured. The majority of events taking place within a reactor release or absorb energy, so if that can be measured it allows a view of … Wikipedia**разность средних температур, определённая при температурном каротаже**— — [http://slovarionline.ru/anglo russkiy slovar neftegazovoy promyishlennosti/] Тематики нефтегазовая промышленность EN log mean temperature difference … Справочник технического переводчика**analysis**— /euh nal euh sis/, n., pl. analyses / seez /. 1. the separating of any material or abstract entity into its constituent elements (opposed to synthesis). 2. this process as a method of studying the nature of something or of determining its… … Universalium**Level of measurement**— The levels of measurement , or scales of measure are expressions that typically refer to the theory of scale types developed by the psychologist Stanley Smith Stevens. Stevens proposed his theory in a 1946 Science article titled On the theory of… … Wikipedia